When long-term disabled heavy fuel fired boiler efficiency, furnace should pay great attention to external corrosion and maintenance problems. First, the boiler shutdown cooling, heating surface must be thoroughly cleaned and the fouling of the upper grate, the lower portion of the furnace ash. Then to maintain a certain degree of natural ventilation flue. In general, in order desiccant moisture should be placed in the furnace, flue. The quicklime as a drying agent, within the furnace or flue gas per cubic meter should be placed generally about 3kg. After placing all the ventilation should be tightly closed doors. After the change of lime powder to be replaced. Low-lying position as boiler room, ground during shutdown severe flood tide, often approach should be used and placed a small fire to dry desiccant combination. If the boiler shutdown a long time, after the complete removal of soot coated with an anti-corrosion red lead paint in oil or other metal surface furnace.
"Fast heavy fuel fired boiler efficiency furnace designed larger, flue gas recirculation provides a reliable guarantee of space. In the burner head design of the special role of combustion, high temperature flame at the outlet of the flue gas interference, be it in the furnace again achieve full combustion cycle (inner loop). this design helps fast boiler leading domestic level in boiler technology, ultra-low nitrogen oxide, the recent large-tonnage party fast brand integrated condensing boiler successful signing in Beijing, and successfully help China build the APEC summit venue. "Fang boiler fast technical director, said.
How to improve the thermal efficiency of gas steam heavy fuel fired boiler efficiency steam boiler to improve the thermal efficiency of gas is a problem many users are taken, I believe this issue is the direction of each used in the production of various types of gas steam boiler manufacturers have been in the study. Many users at the time of the gas-steam oven operates, often in the actual production process, we found some new problems, but all the problems, the most vexing is the high temperature exhaust gas steam boilers, thermal efficiency than low phenomenon that a serious impact on our work, then how should we do to improve the thermal efficiency of it? need to know this is the best way to meet the low-temperature properties of gas and steam comes as synthetic gas steam. However, the vast majority of synthetic gas and steam biphenyls, benzene derivatives of both components of the complex, or a vapor of volatiles has strong carcinogenicity, it is strongly recommended that the client select the type of mineral oil vapor product gas. Second, gas and steam products to meet the low temperature performance process, but also have a relatively high flash point required. In general, gas steam engineers suggest, low temperature gas steam flash point not lower than the opening 200 ℃. After a professional manufacturer of continuous research and improvement of its equipment, in order to improve its thermal efficiency was found to be increased tail gas steam boiler heating surface of, say, air preheater and economizer. But when organic heat carrier furnace return temperature is high, you can not set the economizer, air preheater can only be set to alleviate the situation. So if no gas steam boiler and other heating systems for low temperature heat exchanger, then the only way to improve the energy efficiency is adding air preheater. After adding air preheater can be a corresponding increase in gas flow rate of steam, gas steam boiler in order to ensure safe, reliable and stable work, the thermal efficiency of gas-steam boiler plant will be a corresponding with the increase.
Henan gas heavy fuel fired boiler efficiencys and waste heat boilers have different it as long as the difference between Henan gas boilers and waste heat boilers are: 1 boiler heat source Henan gas is to use the medium of combustion (coal oil gas, etc...) Is obtained, and the heat source waste heat boiler is the use of industrial combustion waste heat waste heat. 2. Structure of Henan gas boiler and a bit more complex ancillary equipment, and waste heat boiler structure is relatively simple, the kind of industrial boilers and more, waste heat boiler is now more straight-through waste heat boiler. 3. parameters Henan gas boiler (pressure, level, temperature) and the like can be easily controlled because the combustion control, the operating parameters of the waste heat boiler is difficult to control, the operation of the heat source is a waste heat boiler with a combustion cycle in an industrial furnace varies . 4. Henan gas-fired boiler is mainly used for gas and steam turbine power generation and other support, waste heat boilers are generally equipment industrial furnace, that there are energy saving and environmental protection.Free Chat
Copyright © 2020.Company name All rights reserved.