If within the natural gas water tube industrial boiler wear how to do? Off If there is detailed examination within the natural gas boiler wear how to do? Detailed examination is the key, fuel management is equally important. According to health and time natural gas boiler, we can plan a reasonable wear health check. When using the fuel, we strictly control the particle size of coal and limestone. Should strictly control the size of the bed material. Boiler waste should be handled. Boiler slag to be treated before discharge. Natural gas boiler should be installed in the heat of use, ease of installation. Hot water pipes should not be too long. It should have a good insulating layer. Hot water output to the end of the pipe should be suitably inclined. A water supply source should be equipped with a control valve. Of emissions, natural gas boiler chimney should extend to the outside, the outlet should be higher than the boiler 1.5 to 2M. If you want to reduce the impact on water wall tube, air pressure and air volume can be adjusted appropriately, effectively reduce the wear and tear of the water wall. Check the standby time is generally down or stop. To check items include leak wear, sealing the furnace and the furnace wall of smoke. In the event of wear, the need for timely repair and welding, to ensure the normal operation of the steam boiler. In general, before the gas-fired combustion of fossil fuels need to be filled in the combustion chamber, fossil fuel and bed material and recyclable materials in air speed, strength and stiffness of the shed fully integrated. Wind bottom means upwardly within the core region. Movement of the outer annular region of downwardly along the walls of the flow of boiler water, thereby prolonging the residence time of the coal particles in the furnace. Mineral particles, large amounts of ash and flue gas contains large amounts of fly ash particles, which continue to cause rapid wear of the water wall tube, wall thickness wear thin, resulting in wear and tear.
Our paper packaging industry from the beginning of reform and opening up to today, we used 37 years to basically build a modern industrial system package. Bring a new era of paper packaging industry is a complicated international environment and arduous domestic reform, development and stability of the new normal, paper packaging industry is facing enormous challenges.
Combustion gas treatment and a malfunction due to gas water tube industrial boiler burner ignition misfire bar: 1, the ignition bar gap interposed carbon residue with oil. 2, ignition rods fragmentation. moist. Leakage. 3, the distance between the ignition does not stick, too long or short. 4, ignition rods Insulation damage, short to ground. 5, ignition cable and transformer failure: cable, connector damage caused by a short circuit during ignition; transformer break or other fault occurs. Gas Burner fails, the action bar ignition misfire following five: Clear, renewal, adjust the distance, change and switching transformer. Second, the gas boiler the ignition spark rod misfiring but the reasons: 1, the disk space ventilation carbon cyclone is blocked, poor ventilation. 2, dirty oil nozzle clogging or wear. 3, the throttle angle is set too small. 4, the firing bar from the leading edge from the oil nozzle tip inappropriate (too protruding or retracted) 5, the first solenoid valve is an oil debris blocking gun (gun small kerosene). 6, oily or too viscous to flow easily clogged or the oil filtration system the valve is not opened, so that insufficient suction pump, oil pressure. 7, the filter pump itself blocked. 8, the oil more water (boiling abnormal noise within the heater). Gas boiler ignition spark rod action but misfiring are: clear; the first washing, such as not renewed; turndown test; adjusting the distance (in 3 ~ 4mm as well); Remove cleaning (cleaning the parts diesel) ; check the pipeline and oil filters, insulation equipment; peripheral screw pump removed, carefully remove the cover inside out net oil, diesel oil immersion; renewal of the test oil. Third, when the gas boiler and turn the fire a small fire normal, off, or flashing the causes of instability: 1, air volume damper setting fire too. 2, oil fires micro switch valve (damper outermost that group) inappropriate setting (set throttle air flow rate is greater than the fire). 3, oleaginous easy to spray viscosity is too high (heavy). 4, and the nozzle plate spacing cyclone inappropriate. 5, fire nozzle worn or dirty. 6, the preliminary fuel tank temperature is too high, so that the steam not smooth oil pump oil feed. 7, gas hot water boiler fuel oil water. When a small fire gas boiler normal and turn the fire extinguished or flashing instability action: Test gradually reduced; heating temperature; adjusting the distance (between 0 ~ 10mm); clean or replace; i.e., set to about 50 deg.] C may be; or drain oil change. Fourth, the noise increases gas boiler burner reasons: 1, cut-off valve is closed or the passage into the fuel shortage, an oil filter blockage. 2, the oil inlet temperature is low, the oil viscosity is too high or the temperature is too high the pump inlet. 3, oil pump failure. 4, fan motor bearing damage. 5, dirty fan impeller. Burner gas treatment increased noise: ① the check valve in the oil line is open, if the oil filter is working properly, the filter cleaning pump itself. ② heating oil or reduce the oil temperature. ③ Replace the oil pump. ④ replace motor or bearings. ⑤ cleaning fan wheel.
What are the ways of heating water tube industrial boiler heating methods currently on the market there are many, but the most common method is still heating boilers, heating boiler to the user's comfort is unmatched by other heating methods. Heating boilers currently on the market are basically three: gas boiler, liquefied petroleum gas boilers and electric boilers. First, the gas boiler Currently, many new residential buildings are used and gas heating. In contrast, the cost is slightly higher than central heating gas heating, but much cheaper than electric heating. Gas boilers and boiler ground into the boiler. The main use of ordinary household heating boiler, convenient and space-saving, low temperature hot water boiler to provide both for the floor heating system, but also to meet domestic water. Second, LPG gas boiler is not connected to the home, use liquefied petroleum gas (LPG) is heated. LPG gas boiler and boiler same, provided only liquefied petroleum gas (LPG) to internal components by changing the gas boiler. However, some series of gas boiler can not be changed, consumers need to purchase the detailed queries businesses. Third, the current electric boilers, wall-mounted electric boiler is mainly used for residential and commercial premises, there is no central heating and gas. When electric boiler may be adjusted to provide warm water temperature itself, but is higher than the gas heating OPEX. According to different models and different installation and heating area need advice whether buying businesses need three-phase power supply into the home. Heating boiler can save a lot of trouble users and more economical than other heating methods, heating is the best way.Free Chat
Copyright © 2020.Company name All rights reserved.