Food factory vertical small coal fire steam boiler should be noted that the ignition of the details need to pay attention when the details of the food factory steam boiler steam boiler ignition 1. food plant should be checked (including related accessories, Management) in front of a fire, and water supply. Before entering the water, the drain valve must be closed. Open air valve can discharge the boiler. 2, the treated water is slowly injected into the furnace, the inlet temperature is generally not higher than the boiler 40. When the water level rises to the minimum level of the water table, the water supply valve is closed, the stabilized boiler water level, the water level drops. With particular emphasis before the fire, you should check carefully the coal port and checkpoints in order to improve compliance with strict sealing conditions. Otherwise, it should clear the debris-side sealing surface, and a good gasket insertion, to ensure that meet strict sealing purposes. Since this is a forced air burner, during operation, gas leakage is not allowed, in order to avoid accidents. 3. When food factory fire steam boilers, open the bottom stoker grate and placed on the wood. After all the checkpoints closed, ignite the lighter. After strong fuel combustion, coal began to increase. When coal burning strong, continue to increase coal, closed after a stoker, hermetically sealed, turn the blower, so that coal continues to burn. burn. Strengthen the observation of the fire, the combustion gradually to normal.
1. Boiler thermal efficiency test: a) determination of boiler evaporation; b) boiler excess air coefficient detection; c) exhaust smoke temperature detection; d) fuel combustion efficiency test; e) boiler thermal efficiency test; f) fuel consumption; g) Steam to coal ratio.
2. Boiler new product stereotyped energy efficiency test: Determine whether the boiler thermal performance indicators are consistent with the design and determine the operation mode of the equipment. Such as boiler evaporation, boiler thermal efficiency, combustion efficiency, various heat losses and so on.
3. Boiler operation adjustment test: Determine the most economical operation mode of the boiler and identify defects in the boiler operation. Such as boiler maximum load, boiler minimum load, fuel requirements, economic load, reasonable exhaust gas temperature, optimum wind coal ratio, excess air ratio, secondary air ratio and so on.
4. Comparative test of thermal performance before and after boiler reform: changes in evaporation, effects of combustion, thermal efficiency of boilers, etc.
5, fuel industry analysis, elemental analysis: to judge the quality of oil, gas and other fuels, easy for enterprises to control the quality of fuel into the plant.
6, water quality testing, scale analysis: determine the quality of water, control the boiler water indicators to prevent boiler fouling.
In the low profit era of Chinese paper packaging industry, entrepreneurs have been turning their attention to internal management, increase business efficiency by saving energy. At present, the paper packaging industry equipment many of them appear old and comes with a variety of issues, in particular energy use seriously inadequate problem is solved and bear the brunt of reform issues. So we must make an effort in the use of energy, use energy-saving equipment for the industry, in order to solve the problem fundamentally.
Necessity textile mill converted to a coal-fired boiler gas boiler is a boiler equipment industry needs is more important, because a lot of links to the papermaking process requires a lot of steam drying, stereotypes and so on. However, along with the national policy of environmental protection departments to ban coal-fired boilers, and now more and more manufacturers have to use coal-fired boilers to coal-fired boilers upgrading or purchasing a new low - NOx emissions. Mills from coal to gas boilers is an important direction of the current transformation of coal-fired boilers, is one of more types of enterprise transformation, especially in the area more natural gas, coal into gas boiler is the main way. 1, in order to transform mechanization layered fired boiler gas boiler, you should first remove the front arch and a rear arch, while increasing the bottom heating surface, instead grate, grate to prevent overheating, combustion; 2, through the furnace heat transfer calculation methods determining the size of the boiler, furnace flame center position, and then pouring furnace work. In order to avoid the center position after arch boiler tubes, based on the original slope of the original arch made pipe. 3, the furnace in order to prevent an explosion, when the coal-fired boiler furnace gas is substituted, or when fuel not atomized combustion gases in the furnace incomplete combustion or heating surface of the end of the furnace, a fire or explosion occurs, should be mounting the appropriate parts of the boiler explosion vent, and to increase the ignition and flame failure protection program control to automatic control means, to ensure safe operation of the boiler. 4, is closely related to the selection and arrangement of the burner and furnace, the filling degree of the flame in the furnace should preferably not to form a dead air. Gas burner arrangement considered reasonable and piping layout, convenient operation, inspection and maintenance;Free Chat
Copyright © 2020.Company name All rights reserved.