As a leader in the fast side condensing gas 2 ton fired boiler in mexico, in recent years, provide a clean boiler to Beijing multiple office units, was well received. I units through the preliminary investigation and contrast, select fast boiler, it turns out, party fast product does have quite a good cleaning environmental performance, in line with the Beijing municipal government requirements for air pollution emissions, the use of very at ease. --customer feedback
Gas 2 ton fired boiler in mexico burner ignition misfire rod reasons gas boiler burner ignition misfire rod reasons: 1, the ignition bar gap interposed carbon residue with oil. 2, ignition rods fragmentation. moist. Leakage. 3, the distance between the ignition does not stick, too long or short. 4, ignition rods Insulation damage, short to ground. 5, ignition cable and transformer failure: cable, connector damage caused by a short circuit during ignition; transformer break or other fault occurs. Measures following five: Clear, renewal, adjust the distance, change and switching transformer.
Electric steam 2 ton fired boiler in mexico combustion efficiency and how to save more: In China container industry is a growing industry, and container industries and enterprises are also faced with various challenges. Container industry must adhere to market-oriented strategy, closely rely on scientific and technological progress, scientific and technological innovation, under the guidance of national energy and environmental policy, company structure and product structure adjustment, manufacture and sale of container in line with market demand, occupancy in the fierce competition in the market place. Electric steam boiler to improve the combustion efficiency, saving fuel, the fuel quality should be controlled, uniform atomization burner. To achieve the above object, the following points should be noted: 1 to understand the combustion principle, adjusting the wind ratio of positive oil (gas), to achieve efficient combustion; 2, to maintain a good working condition of the nozzle, the nozzle is not easy too large or too small, the nozzle wear obstruction, carbon status, to ensure good atomization combustion conditions. 3, to maintain proper pressure or hydraulic, pneumatic or steam boilers, such as high or low oil pressure, and a hydraulic or pneumatic pressure is too large or too small, will affect the mixing of fuel and air uniformly. 4, to adjust the burner flame length brains spray angle size and shape of the combustion chamber with fire furnace chamber filled eye, achieve economic combustion. No black smoke, no soot, in the good sense of the coming year running.
What are the three common 2 ton fired boiler in mexico combustion? Urban coal-fired boiler has been difficult to solve, because especially small coal-fired boilers type cluttered and more widespread particularly difficult to handle. On the one hand burning low power, on the other hand is more a waste of resources. Under the requirements of environmental protection requirements, many cities in the relevant part of the requirements necessary gas (oil) boiler retrofit or replacement of 10t / h coal-fired boilers. The transformation of the former needs to focus attention to the following questions: whether the site is useful region of central heating boiler heating of small alternative program. The useful life and corroded boiler, if the boiler by Zhengzhou fast boiler or other professional testing organization to determine the useful life of less than five years, the transformation of value is not high. Determine whether the laying of gas pipeline convenience, liquefied petroleum gas or other fuel supply and transportation issues. Comparing the cost of renovation and equipment manufacturers advantages and disadvantages, in determining the needs of the transformation plan in compliance with these principles. Selection of fuel. Under the premise of fuel sources have, the most economical natural gas pipelines, liquefied petroleum gas, followed by a final light diesel oil. Also, consider the surrounding environment from fire and explosion safety. In general, the system and the soda boiler pressure parts and preferably not modified to adhere to the original power, are demand, under conditions not substantially change the pressure member, than the original power increased by 10% to 20%. Boiler pressure parts for major changes in the program desirable. The transformation process is necessary to ensure the safety of boiler pressure parts of (mostly small commercial general pressure boilers), followed by incineration system to ensure the safety factor, the decline in the risk of explosion, fire accidents. Recognize the transformation of the planning process, in a timely manner, the environmental protection, the gas company, fire department, urban construction and timely communication with the boiler section to monitor and ensure the transformation plan can proceed smoothly. When the boiler is burning way during boiler selection will take into account an element, the following three common boiler burning approach advantages and disadvantages brief analysis cf: 1 Decentralized incineration strengths: this way is not burning premixed, but the gas nozzle mouth dispersed with each other, and then burning it. Incineration relatively simple way, as more stable as compared to the flame. Disadvantages: Due to a longer flame, it is prone to the phenomenon of incomplete burning, more carbon monoxide and nitrogen oxides will occur, it is not conducive to the use of full-fired boilers, to improve the thermal power of the boiler, and the boiler emissions standards are difficult to reach. 2. premix approaches incineration advantages: premixing air and gas, a multi-way heat radiator, to improve the strength of heat transfer. Strengths of this approach is that the burning of the burning flame is more clear, and the higher heating power. Disadvantages: incineration requires precise ratio premix burning rate is fast, uniform burning radiant heat transfer full power high flame temperature below 1200 deg.] C, all NOx completely burned and the occurrence of low flue gas temperature, condenses, good heat recovery and high power. 3. No flame burning incineration space before incineration approach uniform mixing with the gas in the gas boiler. When using this approach, in the process of incineration gas in the oxygen demand is not made in the ambient air demand, only needs to achieve instant complete incineration air mixture reaches the incineration zone. Approach in the selection of incineration, incineration demand for the advantages and disadvantages of different approaches, carried out mutatis mutandis selection, a good way is also advantageous burning boiler to reach plenty of incineration, thermal power increase, decrease the role of emissions, and therefore, it is important to choose carefully.Free Chat
Copyright © 2020.Company name All rights reserved.