Fast boiler is a research and development, manufacturing, sales of clean fuel boilers and boiler clean combustion technology of high-tech enterprises, including a boiler manufacturing and installation of Class 1 national A-level qualification. ABP has a single-family development center, single-family test center and two manufacturing area, producing a total area of 120,000 square meters, is one of China's boiler industry's leading companies with digital processing power, the products are exported to many countries and regions.
Henan gas boilers and waste heat boilers have different it as long as the difference between Henan gas boilers and waste heat boilers are: 1 boiler heat source Henan gas is to use the medium of combustion (coal oil gas, etc...) Is obtained, and the heat source waste heat boiler is the use of industrial combustion waste heat waste heat. 2. Structure of Henan gas boiler and a bit more complex ancillary equipment, and waste heat boiler structure is relatively simple, the kind of industrial boilers and more, waste heat boiler is now more straight-through waste heat boiler. 3. parameters Henan gas boiler (pressure, level, temperature) and the like can be easily controlled because the combustion control, the operating parameters of the waste heat boiler is difficult to control, the operation of the heat source is a waste heat boiler with a combustion cycle in an industrial furnace varies . 4. Henan gas-fired boiler is mainly used for gas and steam turbine power generation and other support, waste heat boilers are generally equipment industrial furnace, that there are energy saving and environmental protection.
Gas Steam Boiler non-normal stall, a phenomenon and treatment, flame reasons: 1, the operation of the auxiliary power supply or trip interruption. 2, boiler combustion instability. 3, the load is too low, so that the load sharply mill automatic ignition energy loss or failure of combustion. 4, mutant coal, coal volatile or low calorific value. 5, the automatic combustion flame detector failure or failure caused by tripping mill. 6, or blast furnace wall tubes serious improper boiler soot-blowing operation, a large amount of water vapor into the combustion chamber. 7, coal pulverizing system, fuel system failure, resulting in a significant amount of fuel reduction or interruption. Or with a large amount of water in the fuel oil gun blocked too many impurities, low pressure steam or atomized. Second, the phenomenon: 1, a significant increase in furnace pressure, furnace flame monitoring flameless CRT display. See the fire no fire hole, BTG warning window MFT warning lights. 2, the unit load decrease, the steam flow drops rapidly, each segment working medium temperature, the vapor pressure decreases, the value of oxygen surge. Third, the method of treatment: 1, if the MFT tripping protection, should an emergency shutdown processing, stop the supply of fuel. 2, identify the cause flameout, and try to eliminate, to conduct a comprehensive inspection of the boiler, after confirming the device properly, can restart. How early circulating fluidized bed boiler ignition achieve the protection of reheaters? Fire causes of valve failure chemical industry regulation and Countermeasures bearing parts heat treated high boiler common defects due to low bypass the security gate and reheaters failure phenomenon and treatment of condensate pump turbine worm gear failure cause analysis and improvement measures in the pneumatic valve powder operating system instructions on how to implement.
Do you know what it is gas energy saving boiler gas boiler energy-saving and environmental protection Many customers do not believe, how coal energy-saving environmental protection? Zheng Boiler Group today for everyone to analyze environmental history of the gas boiler. Energy saving gas boiler pot Zheng Group production of a new product, a gas chinese coal fired chain grate steam boiler. Energy saving gas boiler pot Zheng Group production of a new product, a gas steam boiler and gas hot water boiler, gas steam boiler models which are mainly DZL steam boiler gas chain, DHL chain gas steam boiler, SHL chain gas steam boiler SZL chain and energy-saving gas steam boiler and circulating fluidized bed boilers. Zheng pot boiler gas saving and environmental protection are "perfect green and environmentally friendly boiler boiler auxiliary boiler machine environmentally friendly application process installation service" model pioneered go on the road "environmental effects Enhancements". In addition to these types of environmental protection boiler, auxiliary equipment, environmental protection is also an important part of the environmental process. Energy saving boiler fuel gas separation efficiency as high as 97.97%, combustible low-quality coal, good desulfurization effect, can significantly reduce sulfur corrosion of equipment, in favor of low quality coal combustion, coal adaptability strong. Boiler fan low energy consumption, high economic efficiency, and can effectively avoid the fan big horse car phenomenon. To more than dust and coal in the coal auxiliary, not only an automatic cleaner, convenient safe, maintenance.Free Chat
Copyright © 2020.Company name All rights reserved.