In the division of the gas boiler is adjusted, if secondary control of the wind speed is too small, it will lead to too close the gas fire, the burner nozzle so that thermally deformed until failure. Other irregularities when adjustment is not timely gas boiler load changes, the upper layer will not cool the secondary damper orifice such burners are burning.
Different evaporator heating surface pressure variation parallel flow resistance of each tube and along the length of the distribution header, and re-position the head can be different between the respective tubes to cause uneven flow.
① variation on the thermal flow resistance. Since the structure of the steam pipe, the quality, of different length, diameter, roughness and curvature, which are not the same resistance to flow, under the same pressure conditions, the size of the resistance will cause uneven flow.
First Affiliated Hospital of Bengbu Medical College, responsible for staff to feedback to our company, this boiler to use less smoke production, in line with the special requirements of the hospital surroundings and national requirements for flue gas emissions. During the boiler installation and operation, square quick technical staff also always concerned about the dynamic boiler, parties can feel really real fast customer service, using fast boiler is assured. --customer feedback
Oil steam boiler water level protection, boiler matching one to two plate water level meter, should always be compared with each other, found that the indicators are inconsistent, must be corrected immediately. The water level gauge shall be flushed in each shift to determine its true water level. At the same time also equipped with water level electrode rod, can accurately collect the water level signal, to send out an alarm or to carry on the feed water pump control.Free Chat
Copyright © 2020.Company name All rights reserved.