The three main factors that affect the quality of the work of condensing gas boiler condensing gas boiler is an alternative to traditional coal-fired boilers star product, now sold on a global scale. But there are still many users mind any doubt, do not know how to improve the quality of their own work condensing gas boiler. Fast boiler condensing gas boiler for many years research, we have made numerous achievements, specially as we summarize the main factors condensing gas boiler quality of the work of three impact. First, specific parameters matching device environment. Condensing boiler and the environment is to ensure system stability closely matches the fundamental, users purchase condensing gas boiler, we must first understand the various parameters of the interface where boilers, thermal energy value, pipe size, the spatial extent of the area and the like may be utilized to determine the type and parameters suitable condensing boilers combined with the original system uses heat energy, so it can guarantee the condensing boiler and the actual use of the environment is in line with the same. Second, following the instructions, the correct operation of the gas condensing boiler. Quality of work of condensing gas boiler is also associated with operating practices, when an operator to adjust the values of various parameters of the boiler and the environment does not match, or the order of the different operations are also likely to lead to confusion when the boiler condensation process, the system Caton, resulting in the condensed water is too large, low pressure, or no change in temperature anomaly. Therefore, before using a condensing boiler and use it is best to have a professional guide and strictly follow the instructions. Third, the maintenance and repair of gas condensing boilers. For condensing boiler maintenance and repair on a regular basis, it is the main reason affecting the quality of its work. To make the boiler run time regular inspection and maintenance, but also to the boiler outage for maintenance, so as to guarantee the normal operation of the boiler when used again in order to maintain a long service life of the boiler. During operation of condensing boiler plant for a variety of factors will result in an exception of equipment failure, operator of proper operation and maintenance of equipment is the basis for stable operation of the condensing boiler, the timing should be for manufacturers of professional technical support personnel to detect maintenance, comprehensive training for operator so that the operator can make timely protection device when abnormal occurs.
Only low pressure hot water boiler supply water temperature is less than 100 deg.] C.
5, pressure boiler circulating pump hot water heating systems, pumping systems engineering is sent to the boiler return water, is generally used in water pump. It has to overcome the resistance of the systemic circulation, but also to maintain a certain pressure boilers, boiler water at high temperature to ensure that no vaporization.
July 26, 2016, Beijing, China Everbright Paper Co., Ltd. and the company signed a "split 6 tons of steam condensing gas detail of 5 ton steam boiler contract" by the company responsible for the WNS6-1.25-YQ split condensing gas boiler steam to all production, installation and commissioning work. The product is the use of condensing technology, effective emission of harmful substances SOx, NOx, COx, is industrial boilers efficient and environmentally friendly solutions.
WNS condensing boiler cleaning errors condensing boiler in which a lot of manufacturing, transportation and installation, due to various contingencies, such that the pipe wall boiler impurities accumulate a lot of dirt, leading to corrosion of the boiler is directly destroyed in the initial operating heating surface. Cleaning the boiler becomes particularly important. Then the process consumers WNS condensing boiler cleaning in which errors can strayed, how to avoid it? Chemical cleaning chemical detection not need to be very careful if problems arise treatment is very troublesome. If chemical cleaning is not complete, the dirt will not be completely clean; if the cleaning time is too long, there have been washing phenomenon; if not good cleaning effect, a secondary cleaning will waste of raw materials, and waste time. Excessive corrosion boiler cleaning will exacerbate the metal to reduce the carrying capacity of the boiler, it affects the future of the normal operation of the boiler. Improvement: chemical analysis and detection of chemical cleaning process must be done, acidity, total iron ion concentration and pH value should be tested once every tens of minutes. When the two closest test data, chemical cleaning end point is reached, and after the acid output. Chemical cleaning which does not inactivate the main purposes: cleaning the surface of the boiler body. Because of more stringent requirements of the control points, if not controlled, it will fail; After cleaning, the cleaning process is simple, easy to produce secondary rust on the surface of a clean boiler, reducing boiler scale and capacity, easy to rust. Improvements: condensing boiler pickling must be washed after passivation. Since the passivation demanding, total iron ion concentration must be strictly controlled during rinsing. After reduction, the iron ions detected to meet the requirements, the PH value immediately adjusted to strongly alkaline, and adding a reducing agent, the temperature was increased. From the above explanation can be seen, there are many non-standard phenomena cleaning condensing boiler WNS Shihai, this period of use of condensing boiler, safe operation, energy production will have a negative impact; to eliminate these negative phenomena, the safe use of condensing boilers and the environment sustainable development has a very large role.Free Chat
Copyright © 2020.Company name All rights reserved.