Wuhan Port District Social Welfare Institute (apartments for the elderly) is invested by the government pension services, with a total construction area of 38,000 square meters, 532 beds, mainly adopt destitute persons, social support on behalf of the elderly. Hope to provide welfare to the elderly year-round 24-hour hot water, the original 2t h boiler in vietnam equipment can not meet this demand, therefore, require additional purchase orphanage hot water boiler. After much investigation, in cooperation with the welfare determined fast boiler, provides three integrally condensing gas hot water boiler (WNS1.4-1.0 / 95/70-Y.Q) by a fast boiler.
WNS 2t h boiler in vietnam burner imported or domestic brands Fortunately, on this issue, different people have different views, some people think that the domestic economy is substantial, others believe that the import is effective and energy-saving. Each has its own advantages, but it is undeniable that domestic and foreign brands burner on the strength is still a gap, because the domestic burner technology started more than foreign, naturally there are differences, the main difference lies in the following points: 1 oil and gas burners aspects of R & D capability, meaning: in Europe and the United States and other developed countries, each burner manufacturer has its own research and development test center to provide strong support, development burner technology . 2. In the low NOx combustion and low nitrogen emissions, the burner domestic enterprises has just started, the relatively low level of technology. 3. In the production and marketing of products of combustion, burner foreign manufacturers to achieve mass production of large, has a great advantage in terms of parts procurement and manufacturing cost control and market promotion. Therefore, the domestic conventional fuel burners in the market is clearly not competitive. At present, domestic burners companies to non-standard products to market breakthrough, it is difficult to form a large-scale mass production. Fang fast wns not only provide domestic gas boiler burner, also available internationally renowned burner Italy Riyadh Road (RIELLO), Decker (BALTUR), Germany Weishaupt (WEISHAUPT), United Kingdom Granville (nuway), etc., manufacturers need to configuration. 4579,
Boiler design efficiency in the engineer design phase, and in general, the actual operation and the initial design thermal efficiency are similar. For example, oil and gas furnace efficiency is greater than 92%, and circulating fluidized bed boiler efficiency is usually higher than 88%. However, boiler efficiency is not fixed. If your equipment is operating at less than design efficiency, then measures can be taken to improve boiler thermal efficiency.
Construction of gas steam 2t h boiler in vietnam steam requirements for the construction of a gas boiler requirements, gas steam boiler installation for the construction of the boiler room have certain requirements, must comply with national requirements in the construction process. Gas and steam 1, the construction of a gas steam boiler room requirements 1) boiler room must comply with the "boiler energy saving technical supervision and management regulations" and "industrial boiler room design specifications" requirement. Gas steam 2) boiler room should have sufficient light and good ventilation, have the necessary antifreeze measures. And boiler room should stay away from schools, housing and densely populated areas. 3) the position should be close to the boiler room heating equipment, in order to reduce head losses and heat loss from the hot oil piping circulating pump. 2, furnace heat carrier device is arranged in claim 1) the sump should be lower than the lowest position of the heat carrier furnace and heat system 1 m, in order to put the net organic heat boilers and systems, sump and furnace heat carrier spacing less than 5 m or separated by a partition wall. It should be fitted with a sump exhaust pipe, which exhaust pipe diameter should be large and specifications than the inflation tube. 2) position of the expansion tank should be higher than the other devices and the piping system, the system must be higher than the maximum bottom level 1.5 m. It should not be installed directly above any one boiler, organic heat carrier to prevent overflow cause a fire. 3) the sump vent pipe, expansion tank, should be connected to the outdoor safety. Can not be mounted on the vent pipe to the valve, to ensure that the tank, the expansion tank to atmosphere to ensure atmospheric pressure operation. 4) the high volume of the expansion tank should be greater than 1.3 times and all the organic heat carrier furnace heat the entire heating systems is at the operating temperature is increased due to thermal expansion of volume. 5) low volume tank furnace heat carrier to be less than 1.2 times the total amount of organic heat. 6) hot oil circulation pump should be at least four weeks for 0.5 m space, and the inspection to ensure the installation routine, the need for maintenance.Free Chat
Copyright © 2020.Company name All rights reserved.