In early 2013, fast boiler is a food processing company Luohe a 10-ton condensing city steam boiler in senegal installed integrally cloud service monitoring module, by monitoring the data found in March, the maximum pressure in the boiler set small deviation, the small boiler load adjustment range, and it uses a continuous replenishment way. When such a large load changes, the burner will start and stop frequently, adversely affect the boiler. After the burner system to monitor working properly, timely communication with customers, to help customers put pressure adjusted to the maximum deviation of the normal range. Then return to the display data safe range, the maximum starting frequency is reduced to the burner 4 times / hour from 8 times / hour, reduced by the mean starting frequency of 3.7 times / hr 1 / hr reported in June. At the same time gas consumption decreased by 10% to obtain the customer's trust and recognition.
How to use gas-fired boiler gas boiler includes a gas water boiler, gas hot water boiler, gas city steam boiler in senegals, gas hot water boiler which is also known as gas heating boilers and gas boilers bath, as the name suggests refers to the gas boiler fuel gas boiler, gas boiler and oil-fired boiler, electric boiler comparison economy, so most people have opted for a steam boiler equipment gas-fired boiler, heating, bath with. 1, boiler water, softening the first, but also to clean the water quality can not be an impurity. 2, gas boiler before the fire, you want to view the valve pipes, steam pipes, water gauge, pressure gauge and drain valve and so on, whether it is intact, whether the normal use. 3 and can not be conditioned to avoid rendering problems. If the gauge to reach the promised 80% working pressure, to avoid excessive pressure. 4, the water table in a glass tube, which should consolidate outer shield, but also to clean and tidy. How should the functioning of the water table at any time of the investigation, if any anomalies should be handled immediately. 5, when the gas boiler shutdown urgency, you want to cancel burning, then closed throttle, then open the door and release valve, the order can not be inverted. 6, when the pressure rises quickly, when and beyond promised to work pressure or boiler annex presents the phenomenon of failure, or a furnace, ducts appear deformed, when leaking air leakage, urgency should be shutdown immediately.
Steam boiler city steam boiler in senegal price Price: works steam boiler is heated in the drum and water is converted into steam, fire gives off heat in the furnace. Qiang boiler plumbing materials sales center is located in the southern suburbs of Datong City, is a design, sales, installation and service of integrated modern enterprise management. The main environmental operating boiler, a steam boiler fired boiler, a heating furnace, steel radiators, cast iron radiators, canned motor pump, the pump piping, air-conditioning water, galvanized pipe, PP board tanks. Details can be found! Works (in Pulverized example) in the furnace pulverized coal combustion heat is first absorbed water wall heat transfer by radiation, boiling and evaporation of the water wall to enter a large amount of steam for steam separator drum (excluding the DC furnace), into the separated saturated steam superheater heated by flue gas at the top, and the horizontal flue gas flue continue to be absorbed radiation and convection, superheated steam reaches a predetermined operating temperature. Generating boilers usually equipped with a reheater is heated by high pressure steam cylinder. Reheater steam power generation is continued into the low pressure cylinder. 1, the working principle (as an example in pulverized coal fired boilers) in the furnace pulverized coal combustion heat is first absorbed water wall heat transfer by radiation, boiling and evaporation of the water wall to enter a large amount of steam for steam separator drum (except for the DC furnace ), the separated saturated steam enters the superheater heated by flue gas at the top, and the horizontal flue gas flue continue to be absorbed radiation and convection, superheated steam reaches a predetermined operating temperature. Generating boilers usually equipped with a reheater is heated by high pressure steam cylinder. Reheater steam power generation is continued into the low pressure cylinder. 2. Pulverized coal boiler operation, the position of the center of the flame will affect evaporation. Generally, low center of the flame will lead to greater evaporation, and the high center of the flame will lead to slow evaporation. Also affects the position of the center of the flame superheated steam or reheat steam temperature. Typically, superheated steam, in particular the reheat steam temperature in the lower center of the flame, and vice versa. 3. Pulverized Coal Burner front and rear walls is arranged a thrust manner, tangential firing mode, bis tangential firing methods, each method has its own characteristics. Since the above-described arrangement can not be applied in the same furnace at the same time, the influence of steam can not be directly determined.
Strict accordance with the operation of the gas city steam boiler in senegal feed water softening process is provided gas steam boiler fouling not only reduces the thermal efficiency of the boiler, but also increases the temperature of the boiler heating surface, damage to the heating surface, even causing the boiler explosion. Thus, soft water treatment equipment, strict accordance with the operation of the boiler feed water softening processing apparatus, the control of boiler feed water quality, delay the formation of scale. At the same time, real-time control the size of the boiler, boiler scale control, cleaning the scale, if necessary, it is very important. Since the gas steam boiler and vapor - water heat temperature is higher than the temperature of the air system of the boiler room, part of heat to the surrounding air by radiation and convection, which became the heat loss. boiler. Accordingly, when the insulating layer and the heat pipe of the boiler system damage or leak is detected, it should be repaired, to reduce heat losses. Steam boiler burner gas noise increases, mainly because of lack of or close the valve in the oil passage into the oil, oil filter plugging; or into the oil due to the low temperature viscosity is too high or oil pump. Temperature is too high; oil pump failure; fan motor bearing damage; dirty because the turbine wheel, the device too loud. When said failure when using gas boiler, and since the viscosity of the oil is too high, atomization is not easy (heavy oil); and because the distance between the nozzle and the cyclone unsuitable; In addition, since the burner worn or dirty; also because reserve tank temperature is too high, leading to the oil pump steam; oil boiler or because the oil is hydrated. Gas steam boiler feed water containing various impurities and calcium and magnesium scale substances, boilers inevitably expanded. Very low thermal conductivity of the scale, once contaminated surface is the surface heat, the exhaust gas temperature of the boiler will increase, and due to the increase in thermal resistance, heat loss of the exhaust gas will increase. Experimental data show, 1mm scale formation in boiler heating surface, the heat loss of the exhaust gas will increase from about 2-4%. Scale thicker boiler heating surface, the greater the resistance, the lower the thermal efficiency of the boiler.Free Chat
Copyright © 2020.Company name All rights reserved.