Image gas boiler for greenhouse (4) of the fan impeller, air guns fire tube, damper controller, damper baffle, a cam adjusting mechanism diffuser plate. 2, the ignition system functions in that the ignition system ignites a mixture of air and fuel, its main components are: the ignition transformer, the ignition electrode, a high voltage electrical cable fire. A more secure electronic ignition system called ignition pulse, is widely used Zhuoyi energy saving gas boiler manufacturers. Which facilitate saving, can simply press a finger, and safe, does not occur due to unexpected accidents occur flame, once the stall state occurs, the control system can close the solenoid valve, off the gas passage. 3, system monitoring function monitoring system is to ensure that the burner safe and stable operation, the main components are flame detectors, pressure monitor, temperature monitor (see below) and the like. 4, functions of the fuel system of the fuel system is to ensure that the desired fuel burner. The fuel oil burner system are: tubing and fittings, pumps, solenoid valves, nozzles, heavy oil preheater. The gas burner mainly a filter, pressure regulator, solenoid valve, and then firing solenoid valve, the fuel valve. 5, electronic control system electronic control system command center and the focal the above system, the primary control element is a control box, for different burners with different programmable devices, the common programmer has: lfl series, LAL series, loa series, LGB series, the main difference is the time of each different program steps. The controller 1, ultra Encyclopedia Chinese LCD display, built-in luminous incandescent lamp, regardless of the day night, the screen clearly visible. 2, the image level animation display state, condition, valve status, alarm status, operation of the boiler at a glance. 3, cpu intelligent central processor, all the programs focused on a digital chip, scalability, high degree of automation, simple, and powerful. 4, includes a time setting, temperature setting, setting valve, a continuous setting, timer setting, and other control functions pressure setting, arbitrarily set the working state.
Steam boiler for greenhouses and thermal oil heaters which is better? Which is more energy-efficient? Steam boilers and thermal oil heaters, which is more fuel cost savings? At the same power (represented with evaporation) for comparing the boiler, HTF medium because of the high temperature, so that the temperature of the steam exhaust gas temperature than the exhaust gas with a higher heating power of the boiler, the exhaust gas temperature directly affects Thermal efficiency. That same power (represented with evaporation) conditions, the efficiency is not high efficiency oil boiler steam boiler. In fact, now you finally choose what kind of boiler is required to rely on the temperature of your decision. If you ask a medium temperature to 300 degrees, you can only choose oil furnace; if you think there is a live medium temperature of 180 degrees is enough to use, it is recommended that you choose a steam boiler, because it is more energy-efficient with conditions). These are the kind of steam boilers and thermal oil heaters and today we analyze all the information of more energy-efficient, and the above information indicates that the steam boiler more energy saving, more fuel-efficient.
Fangkuai Boiler has more than 200 after-sales service outlets across the country. Each after-sales service outlet is equipped with a professional boiler for greenhouse technical engineer, providing 24-hour emergency repair services, and has sufficient spare parts and wearing parts all year round, convenient. Customers change in time.
Using imported burner, automatic programmed control, automatic purge blower, electronic auto-ignition, spontaneous combustion and gas, (air) to automatically adjust the proportion of oil wind, good atomization, combustion, energy saving, have flame protection device ensures combustion safety. Under normal circumstances, the combustor output temperature of the boiler for greenhouse with the combustion flame length is automatically adjusted, the outlet temperature of the boiler reaches the set value, the burner combustion is automatically stopped, when the temperature is below the set value, the burner is automatically started. When the abnormal phenomenon of the fuel, air intake, fault lights, the output sequencer will immediately stop the fuel, burner shut down automatically.Free Chat
Copyright © 2020.Company name All rights reserved.