Using Ultraten wings condensation boiler technology has greatly enhanced heat the heating rate; silicon alloy material design to achieve the depth of the condensing heat exchanger, high efficiency, high heat transfer speed. "APH the T7" ready to use the factory mode, the system design is simple and clear, i.e. security that is used, the best burner performance debugging the factory, the user can simply set up at the installation site, connected to gas, water, to a flue , it covers an area of greatly reduced.
Operation of the boiler, including what? Including the operation of the boiler, what does? Following on from the Henan fast boiler company to tell you about: 1. The water level regulation of normal water level in the middle of the gauge (1) of the boiler. Operation with the magnitude of the load is adjusted: to maintain a high level during low load, high load to maintain a low level. Changes should not be down more than 40 mm. (2) to be run on the water level gauge to compare the two groups, if the water level display should be corrected promptly identify the cause. (3) To achieve a balanced continuous boiler feed water, ground water supply, water supply less, to maintain the water level in the normal water level fluctuates slightly in the vicinity. (4) load change is large, prone to false level. Pay attention to judgment, in order to avoid misuse. 2. Steam pressure regulator (1) when the boiler must constantly monitor the pressure gauge indicated. To maintain stable steam pressure, boiler pressure must not exceed the design pressure. (2) increasing the boiler load: Steam pressure decreased boiler load is increased, if the level is high at this time, the amount of water should be reduced to a water supply or suspend, the amount of coal and increase the air volume. Gradually increase the amount of water at the same time to strengthen the burning, keep the steam pressure and the water level is normal. (3) boiler load reduction: the vapor pressure rises to reduce boiler load, if the level is high at this time, the amount of coal should be reduced and the air volume, reduced combustion. Then the appropriate water reduction or suspension of water supply to the water vapor pressure and stability in the nominal range. Then press the normal combustion and to adjust the amount of water. If the actual water level within the boiler is low, to increase the amount of water should, until the water level returns to normal after the combustion and needs to be adjusted according to the water vapor pressure and load changes. 3. Combustion adjustment (1) combustion index. Normal combustion boiler comprises a uniform supply of the fuel, reasonable ventilation, adjusting three basic aspects combustion. B. maintain a high temperature of the combustion chamber temperature of the upper layer is preferably in the 1100-1300 ℃, flame orange in color. Flame reddish color indicates that the amount is not enough to the wind, the color white indicates that excessive wind. It should be appropriately adjusted. C. fuel ash to reduce ash content in the combustibles to be below 10%. d. reducing the temperature of the exhaust gas boiler exhaust gas temperature should be controlled below 200 ℃. e. excess air negative pressure holding furnace boiler 1.2-1.4, by adjusting the balance of the blowers to maintain the furnace pressure is 2-3mm. F. to improve the thermal efficiency of the boiler thermal efficiency of the boiler should be kept above 60%. (2) adjusting the combustion a. Reasonable amount and the distribution of fuel to the amount of air needed for combustion. Ventilation should first increase the amount of fuel increases, it should first reduce the amount of fuel supply reduced ventilation. b wind principle feature: burn promoting intermediate ends. That is, after the coal into the coal starts to warm up the shutter, fire line front arch, the primary combustion zone, the middle grate to burn the rear grate zone. c is the normal combustion conditions: fuel ignition start at 300mm from the shutter of coal, even flames, the fire bed formation, at the end away from the combustion grate at the end of 300-500mm. d. Hold appropriate furnace temperature to avoid coking. E. fire bed to maintain the homogeneous combustion, to avoid burning fire bed obliquely. F. less than 30 minutes residence time of the fuel on the grate. Our company provides services related to the installation of the boiler!
In the national standard of water quality standard, the water quality index of heating hot water boiler stipulates that the total hardness of water supply for chemical treatment outside furnace is less than 0.6 mmol / L. In recent years, in order to reduce the operating cost of heating units, some hot water gas-fired steam boilers have been overloaded due to the use of class Ⅲ bituminous coal as fuel instead of class Ⅱ bituminous coal designed to replace the designed type Ⅱ bituminous coal. During the maintenance in summer, it is found that the overloading boiler water wall tube fouling problem is more prominent, some boilers even occur tube burst accident. Why is heating hot water boiler overloaded, scale and even burst tube? Because the calorific value of class Ⅲ bituminous coal is higher, the type Ⅲ bituminous coal of the same weight is burned instead of the designed class Ⅱ bituminous coal. Bituminous coal increases the circulation of boiler riser is not absolute equilibrium, the geometric difference of riser and the heat load are different, so there is inevitably the deviation of flow rate between the risers. Due to the overloading operation of the boiler, some riser tubes are easy to overheat boiling because the flow rate is small, and the wall temperature is higher than the designed wall temperature, so that the scale and even the tube burst are easy to occur. How to prevent the boiler from scaling when overloaded? The heating hot water boiler operates under overload because of the scaling after the superheated boiling. Steam is produced in the process of superheated boiling. The water quality requirement of gas steam boiler is less than 0.03 mmol / L, which is much lower than that of hot water boiler. Water quality requirements. Based on the above reasons, the feed water hardness of heating hot water boiler is reduced, and the scaling phenomenon is eliminated by reducing 0.6mmol/L to 0.03mmol/L.
Preparation and method for measuring the moisture content of the flue gas of the boiler before the boiler purchase this product knowledge and understanding, the present, it is necessary for two reasons, first, it is the site of important product and the main key one word, and second, the products are widely used, why we have these conclusions and specific requirements. Meanwhile, I hope that we can be taken seriously and, in order to have learned well and apply their knowledge to practical work flexibly. Is there some preparatory work before the boiler 1. buy? Boiler products to buy, this is an important job, and need to be taken seriously, but also want to take into account all relevant factors, in order to have accurate judgments and the correct choice, a good choice to avoid mistakes. Before carrying out this work, is the need to do some preparation, use of the product to the environment and have a clear understanding of the requirements and learn about product origin, specifications, technical parameters, materials, quality, price, service and product manufacturers these and other basic information, in order to compare and consider, then, the right to choose their own products. 2. whether Sheung Shui before the boiler starts have specific requirements? From a professional point of view, Sheung Shui before the boiler starts, there are some basic requirements, which specifically is: If the heating hot water boiler, the water speed before it starts not too fast, not be less than the winter time Sheung Shui 4 hours, in other seasons upper water time of not less than 2-3 hours. And, at the beginning of the water, its water speed to slow. If the boiler is cold, it's inlet temperature in the range of 50 ℃ -90 ℃, and the difference between the water temperature and the temperature of the drum wall into the steam drum, not greater than 40 ℃. 3. What is the chain boiler? Chain boiler, which is a particular kind of a boiler, a higher degree of mechanization layers fired boilers, the time the track grate with a chain similar to these so called chain boiler A boiler. Further, it is a pre-boiler, the coal combustion process is completed in the movement. Advantage of this kind of boiler, the combustion condition is stable, high thermal efficiency and easy operation, in addition, its low concentration of dust emissions. However, it should be noted that the moisture content of the larger, more ash and strong coking coal, not suitable for this kind of boiler for combustion. 4. How the moisture content in the flue gas boiler measured? Determination of moisture content in the boiler flue gas, which is the weight measurement method, condensation method, and three psychrometer, and the moisture content of the flue gas is typically in the volume percent of water vapor in the flue gas content to represent. If dark gravimetry, need to use hygroscopic agent, the hygroscopic agent used is calcium chloride, calcium oxide, silica gel, alumina, phosphorus pentoxide, magnesium perchlorate and the like.Free Chat
Copyright © 2020.Company name All rights reserved.