Small horizontal fired steam boiler Description: Small steam boiler refers to the amount of evaporation per unit time is small and low steam pressure steam boiler, steam boilers generally small volume refers to less than 30 micro-liters exemption steam boiler, the mechatronic device, host auxiliary integrated, easy to use, simple to install, simply connect the power, water and heat can, installation, use and technology supervision department supervision is not. Working principle: Its basic principle is: by an automatic control device, to ensure control liquid during operation or high, medium and low probe feedback control electrode opening of the pump, is closed, the amount of water the length of time the heating furnace; it is set by the pressure switch with the constant maximum output vapor pressure steam, the water level falling furnace, when in the low water level (mechanical), water level (electronic), automatic water pump, to the high level, the pump is stopped replenishment; At the same time, the electric tube furnace heating was continued, a steady stream to produce steam, the upper portion of the top panel or instantly display the steam pressure gauge pointer value, the whole process can be automatically displayed by the indicator. Product: Small steam boiler in accordance with the fuel can be divided into small electric steam boilers, small fuel steam boilers, steam boilers and other small gas; in accordance with the vertical structure can be divided into small steam boilers, horizontal steam boiler small, mostly single small steam boiler , double the return of the vertical structure, large steam boiler three-pass mostly horizontal structure
Natural gas horizontal fired steam boiler by what configuration consisting of environmental policy and natural gas high pressure steam boiler their good performance advantages, let natural gas steam boiler stand out in a crowd boiler types, all ages, and use more and more users. Many users before purchase natural gas steam boiler, the boiler due to insufficient understanding, very easy to be deceived poor sales. Today we have to say something about, what are the natural gas steam boiler configuration consisting of it so that we have a general concept. Natural gas steam boiler is a series of devices can be roughly divided into two main parts and auxiliary equipment. First, the main member 1, the chamber: the fuel burn-up and ensures that the boiler outlet temperature of the flue gas is cooled to a value of convection heating surface capable of security. 2, the drum: the respective heating surface and joined together and the boiler water wall tubes and other components decreased water circulation circuit. Soda storage drum, can adapt to changes in load, with internal steam separator means to ensure the quality of soft drinks, no DC boiler drum. 3, water wall: mainly radiation heating surface of the boiler, the absorption of radiant heat furnace heated working fluid to protect the furnace wall and the like. 4, combustion equipment: the fuel and air required for combustion of the fuel into the furnace ignition and stable good combustion. 5, air preheater: heating the fuel with air, in order to enhance ignition and combustion; flue gas waste heat absorption, reducing the exhaust gas temperature, increase boiler efficiency. 6, the furnace walls: a housing to protect the boiler, since sealing and insulation. Heavy furnace wall of the small boiler may also function as a support member boiler. 7, the frame: a support member and fixing the boiler. Second, the auxiliary device 1, the wind equipment: induced draft fan and chimney via the flue gas generated in boiler operation sent to the atmosphere. 2, dust removal equipment: removing fly ash in the boiler flue gas. 3, the fuel supply apparatus: fuel storage and transportation work 4, water supply equipment: a water pump to feed water through the water treatment device into the boiler. 5, the air blowing apparatus: the air blower means through application exports the furnace air preheater and a coal grinding heat. 6, the automatic control device: automatic detection, process control, automatic protection and automatic adjustment. Natural gas steam boiler is mainly from these major components and auxiliary equipment components, making them a reasonable match to achieve efficient boilers, environmental effects, but also improve the thermal efficiency of the boiler, the boiler at work so that you can achieve safe and reliable results.
R & D center built and put into use, is a landmark event in the party group was founded two decades of fast, fast Group is party to enhance the quality of another milestone, is quick to understand the user side of the new window, it is to demonstrate a new gas boiler technology platform. Fang fast development center connotation of high-tech feel, quite the image of modern atmosphere, welcome your visit and visit!
Water wall boiler tube leak or burst phenomenon how to do 1, the normal water flow is not greater than the steam flow. 2, the furnace pressure transient and unstable prejudiced. 3, tube leak detection alarm device. 4, the furnace may not tight at the outward discharge gas and water vapor, and a significant leakage sound. 5, the main steam pressure drop. 6, boiler combustion dark flame instability caused by severe boiler fire. 7, when the induced draft fan is automatically cast, abnormal static vane opening is increased, the current increases. 1 reason, the presence of water wall tube material defects or post-production, the installation of the damaged pipe, poor welding quality. 2, the inner tube fouling overtemperature. 3, the inner tube corrosion. 4, water wall wear. 5, the long-term high load operation, furnace coking, coal sulfur corrosion caused by high temperature water wall. 6, improper combustion, flame deflection. 7, in the possession of bad foreign body, the water cycle. 8, the wall of the long-term over-temperature operation. 9, the temperature difference between waterwall tubes, mechanical stress crack. 10, the normal exit or drain sootblower steam punctured tube. 11, smashed chunks of coke furnace water wall tube or serious explosion occurred, resulting in water wall tube suffered external damage. 12, boiler overpressure long run. 13, the boiler starts to heat up, step-up too fast. 1 process, the leakage should try waterwall tubes outage. The leakage is not serious, while still capable of maintaining operation, note that each of the automatic operation when the device, if not normal, it is cut immediately to the manual, if necessary, may be down, down-load operation. Closely monitor the development trend of damaged parts, good accident anticipation, application shutdown as soon as possible. 2, if the leak is serious, the bursting point temperature after a sharp rise in quality work, leading to serious over-temperature wall, unable to maintain the normal operation of the boiler or threaten the safety equipment, emergency shutdown provision should be processed, when the steam temperature to protect the action value, the protection does not move, should immediately hand MFT. 3, note that the operation of the electrostatic precipitator, to strengthen the inspection checks, to prevent fouling, and the electrodes ESP hopper, pipes and the like plugging air preheater ash. 4, after the shutdown, should retain ID fan, the furnace pressure is maintained constant, there is no discharge to be stopped after soda ID fan.Free Chat
Copyright © 2020.Company name All rights reserved.