Now intelligent boiler equipment, modular design arrangement, the parallel combination of the simple, multi-joint control boiler. Users can produce according to demand, real-time adjustment of the number of operating boilers, to a great extent to meet the different techniques, different steam using steam differentiated, personalized requirements; comprehensive energy saving can reach 30%.
Diagnostic how to produce dry industrial boilerssteam boilerhot water plant accident when the lowest water level of water already defined inferior, but still water meter water level can be seen, less water mild off; when the water level was observed water level gauge see when broken into serious water shortages. Status summarized as follows: (1) a conventional water drum level height inferior to the height defined; (2) low water warning, alarm sound, warning lights; (3) the temperature of the steam superheated vapor is increased; (4) providing water not conventional, less than the amount of steam; (5) the temperature of the water vapor discharged smoke increases.
It provides fast side of boiler equipment, installation and commissioning after all normal, we immediately put into use, the hotel did not delay the normal heating. Meanwhile boiler capacity, energy efficient, fully able to meet the needs of heating and bathing water in our hotel rooms. --customer feedback
Installation Notes boiler environmental protection boiler should not be installed in the bedroom or the bedroom figured the room. To facilitate installation and maintenance, in place boiler, the boiler and the maximum dimensions of the object, or four weeks from the wall should be less than half a meter. Placing the boiler ground should be flat, rigid, to facilitate drainage. When the boiler is mounted in place, holding the top surface portion of the boiler capacity is lower than the rear 5-10 mm. Displacement and ensure that the boiler does not occur after the sinking operation. The environmentally friendly heating system installation design are by atmospheric boilers, pressure must not be used. Heating the water temperature should not exceed 85 ℃. Circulatory system supply and return water pipe diameter must be consistent with the boiler supply and return water connection diameter shall not be reduced. Supply and return water pipe should maintain a reasonable aspect and slope, main boiler return pipe direction should bow, maintenance, overhaul, should be able to put more than water to make the system. Up and down the main supply pipeline should avoid bending, bulging, protruding local phenomenon. The pipe through the wall, slope liable to change, install with caution. Boiler expansion tank is not less than the total volume of water systems and boiler circulation pump 15 is mounted% 6: circulation pump should be installed on the main supply mains closer to the boiler, a circulation pump to be provided on both sides of the pipeline valve, to facilitate maintenance. Using temperature Importers hose connected between the valve and the pump, to eliminate the noise generated by the circulation pump. It should be set at the same time the bypass conduit, the main supply pipe the same diameter, provided on the changeover valve. During normal use of the heating circulation pump, the bypass line switching valve should be closed. Should be converted to the natural circulation loop by a pump switching valve to open the bypass pipe line, and then close the circulation pump. Bathing mounting system: the system is connected with one end export bath, the other end is connected to the water pipe. When not using this function, you do not have to do anything. Chimney installation: chimney diameter of the mounting height is not less than the list of technical parameters on the boiler chimney. Chimney installation should be vertical, vertical hanging test method may be employed. If deviations can be leveled at the flange connections correction, and to ensure the sealing effect, and the ground support chimney, furnace chimney connection must be firm and reliable. After the chimney installation having a diameter of 5 mm or more of the three wires or cable tension, the degree of tension should be substantially the same three wire. No exceptional circumstances may not set a lateral chimney. If space constraints, you must set the lateral turn, should ensure that the chimney lateral angle from the horizontal portion of angle no greater than 50, the remainder of the vertical. Should be appropriately increased stack height laterally long.Free Chat
Copyright © 2020.Company name All rights reserved.