Steam boiler rules Henan fast boiler with small series to introduce the company's wns series fired oil fired steam boiler operating procedures. First, the components of the steam boiler before oven cooking oven and check (a) and oven cooked boiler furnace must be checked in detail. Check the following items: 1, cold chain grate test more than 24 hours, cold test should meet the following requirements: (1) grate should be smooth turning chain wheel axle, found arched, two tension bolts can be tightened. (2) the active grate sprocket good occlusion. Minimum gap (3) on both sides of the active grate block with the side seal and the side seal angle not less than 6 mm. Distance (4) on both sides of both ends of the furnace grate platoon leader pin in the sprocket should be kept equal. If it is found at one end to the occurrence of side friction, long waist-hole may be a tap with a hammer, the end surfaces on both sides remains equal distance. (5) steam boiler grate rotated without jamming, deviation phenomenon, when the deviation found by the inspection hole into the rear grate tail, the tie bolt align the two bearings of the drum, deviation phenomenon can be eliminated. The boiler has ignition combustion, still need to transfer found Hearth n, just before two adjustable chain tensioning bolt shaft directly outside the furnace, but preceded align the front sprocket shaft and a gearbox connect the safety pin or bolt removed until after squaring shaft to a gearbox with a chain alignment pin or bolt after tightening, may otherwise result in misalignment with the sprocket shaft of a gearbox and mechanical damage. (B) Check broken grate furnace platoon leader pin is bent, if long waist hole in the furnace may be carried out at any time platoon leader pin alignment reload. (C) a chain grate does not allow foreign matters (such as bolts, nuts, nails and other iron) is present. (D) firing door open and flexible, easy to open and drop the shutter coal, coal gate left and right side of the grate surface distance equal to, the thickness of both sides of the seam to ensure equal furnace, as a method for reducing ranging from links available to make equal, coal shutter cover plate should cover tightly to prevent leakage into the coal, coal stuck shutter. (Five) of each grate windshield of smoke damper and damper adjustment inside the flue flexible switch. (Vi) blower, Fan, Java machine, commissioning normal water supply equipment. (Vii) manhole, hand hole is tight, attached parts fitted Ge are complete. (Viii) the furnace wall is normal, the flue is tight. (Ix) steam boiler pipes, water pipes, sewage road is complete. (J) all filled with lubricating oil in the bearing housing and oil cup. (Xi) All electrical equipment should be empty running test, inspection equipment, and other electrical lines is intact.
In the fierce competition in the market, fast boiler adhere to "not forget the early heart, sustained ingenuity" of the faith, taking the long view, establish and improve a comprehensive overall solution, leading to control market trends, improve the environmental performance of the boiler, make unremitting efforts to build China clean boiler brand.
Gas wns series fired oil fired steam boiler not only focus on their own function and more environmentally friendly gas-steam oven due to heat and heat transfer equipment, and for many professions. Screening of its upgrade and shopping centers is very high, and even some of the new products will be screened in a few years. If we can not meet these requirements, this highly competitive industry on the development of the oil furnace put forward new requirements. If you do, you will certainly face a screening room. Today's gas-steam oven not only focus on their own function, but also more environmentally friendly. As long as the bow is in line with today's society about the development of high-tech products, otherwise it will be empty talk. Insulation gas steam oven is a very important factor to measure the value of its shopping centers. Steam oven gas having good insulation function expensive than about 20% of oil furnace insulation function difference. Do not underestimate the 20% of the costs and profits. A very scary figure. Gas insulated steam oven is mainly reflected in its interior. Some oil furnace with a heat insulation material, which is integrated with the oil furnace. They do not conflict with other raw materials. Let's talk about this oil furnace. The product is called high-tech insulation oil furnace products. Because it is equipped with a high-quality insulation material, and therefore require a longer heating temperature and longer data to assist the burning material processing company. The purpose is to save money for the company. At present, commonly used as a furnace gas and steam insulation materials include products of rock wool insulation panels, foam insulation board cement, Portland composite panels and aluminum panels. We expect a wide range of gas-steam oven manufacturers will focus on the selection of the insulating material. Them into account, because they are really suitable for insulating oil furnace.
Gas introduced gas wns series fired oil fired steam boiler steam boiler stop sign Profile: natural gas steam boiler is a steam boiler gas, natural gas steam boiler with natural gas as fuel, the combustion in the furnace heat put out by heating the pot water, and allowed to vaporized into steam energy conversion device. Water pan (drum) is continuously released from the combustion of a gaseous fuel energy to heat the furnace temperature is increased and produce steam under pressure. Since the boiling point of water increases with increased pressure, the pot is sealed, the expansion of water vapor generated inside the pressure limited thermodynamic formed, strictly speaking, the steam boiler is heated in water at constant pressure saturated steam drum regasification water formed, is widely used as an energy source. Protection device: (1) protect the boiler water a boiler water level gauge plate supporting one to two, should always be compared with each other, inconsistent findings indicate that shall be corrected immediately. Class water level should be flushed, to determine their true level. While the water level comes electrode rod can accurately capture level signal to an alarm or a pump control. (2) steam pressure protection pressure controller: selection of high sensitivity of the pressure controller, the pressure is high, or low levels of signal to the electrical switches, other control lines or automatic control chain protection. Using pressure controllers and electrical contacts, the vapor pressure can overpressure alarm; single adjustable pressure controller or dual fire burning fire the actual operating pressure. Safety valve: safety valve is the last line of defense to protect the boiler, the boiler pressure exceeds the limit, according to the set pressure relief valve design with the school, the exhaust steam pressure relief, to ensure the normal operation of the boiler. (3) having a burner flame protection flame protection inlet means, combustion function is to detect, when the ignition failure or extinguish combustion middle, immediately off the burner into the oil (gas) solenoid valve, the blower continues to operate at this time, the furnace was purged combustible residual gas, after 20 to 30 seconds purge, and various auxiliary blowers automatically cut off power, the boiler operation stops. (4) self-locking power failure protection case, the boiler shutdown immediately burst self-locking power interruption, if the current power is restored, the boiler will not start at any time, you must reset release self-locking, to re-start the ignition. Editing boiler ignition procedures: 1. Check operation and (or) shift recording. 2, inspection, examination boiler, external. 3, check the main safety accessories. Safety valve, water gauge, pressure gauge, to be tight, reliable and sensitive. 4, check the water treatment equipment. 5, inspection equipment and soda water supply system pipe. Adjust the valves as required to start. 6. Check the oil supply equipment. After the above inspection qualified, you can start the boiler. Note: The boiler is a high-temperature, high-pressure thermal equipment, is one of special equipment, widely used in government agencies, public companies and all walks of life, it is dangerous and special equipment. Event of an accident involving public safety, it will cause huge losses to the state and people's lives and property. For public safety, people's lives and property safety, according to the State Council, "Regulations on Safety Supervision of Special Equipment", the boiler should use full attention the following matters: 1, should be accompanied by safety technical specifications of the factory boiler design documents, product quality certification, safety and the use and maintenance instructions, supervision and inspection certificate (safety supervision, inspection and performance certificate). 2, boiler installation, maintenance, alteration. Engaged in the installation of the boiler, maintenance, renovation of the unit shall obtain special equipment installation and maintenance certificates issued by the Provincial Quality and Technical Supervision, before engaging in the boiler installation, maintenance, alteration. Construction unit before construction will be prepared for installation, maintenance, alteration in writing inform the special equipment safety supervision and management department of the municipality or district, and will start informing sent to the local county level Quality and Technical Supervision for the record, told immediately after construction. 3, inspection of boiler installation, maintenance, transformation. After construction, the construction unit To State Quality and Technical Supervision of Special Equipment Inspection and hydrostatic testing of the boiler installation supervisory inspection declaration. After passing by the State Quality and Technical Supervision, State Special Equipment Inspection, County of Quality and Technical Supervision involved in overall acceptance. 4, registration boiler. After the boiler inspection, the use of units must be in accordance with the "special equipment registration and use of management rules", fill "boiler (census) Registration Form", the State Quality and Technical Supervision to register and obtain a "registration certificate to use special equipment safety . " 5, operation of the boiler. Boiler operation must be performed by trained and qualified to obtain "special equipment operator certificate" certified personnel to operate, must strictly abide by the rules and eight systems, six record. 6, check the boiler. Periodic inspection of boiler once a year, not be used without safety periodic inspection of boilers. Safety accessories safety valve of the boiler regular inspection once a year, pressure gauge biannually verified, may not be used without the periodic inspection of the safety accessories. 7, non-pressure boilers will be installed for the boiler pressure. Do not use water level gauge, safety valve, pressure gauge three safety accessories insufficiency boiler.Free Chat
Copyright © 2020.Company name All rights reserved.