Gas oil furnace fuel additive effect and the boiler room Notes: Gas oil furnace, oil furnace that is both in one, and, still in the boiler in this category, so, based on this, the following will continue be familiar with and understand the boiler, because it is the product website and keywords. Moreover, we can also derive some new knowledge, in turn, make progress and development in their learning path. 1. Gas oil furnace, which is a fuel additive, then what good? Gas conducting oil furnace, in which fuel additives, it is possible to optimize the fuel, and reducing soot and improving thermal efficiency. However, it should be noted that, in addition amount to control the well, in moderation, too much or too little, will always have problems, thereby, affecting the normal combustion of the fuel. 2. Gas-fired 6t fired steam boiler for industry and gas oil furnace, boiler room can both jointly built it? Gas-fired steam boiler and gas oil furnace, two boiler room, is jointly built, and that is no problem. However, it should be carried out in accordance with the steam boiler room equipment specifications and oil furnace room design specifications, avoid mistakes, and at the same time, to make the two boilers, a good use of effects.
Tail secondary combustion flue how to deal with the phenomenon of a sharp increase in rear of the boiler flue secondary combustion flue temperature location and later. 2, the furnace, the flue abrupt change in negative pressure, flue gas is not tight at the smoke, the Mars. 3, air preheater large current swing bearing housing temperature, severe Jam occurs. 4, air preheater fire alarm issue. 5, steam temperature, economizer outlet water temperature, the air temperature rises abnormally. 6, induced draft fan vanes automatically open a large, Fan current rise. 7, as the combustion side, both sides of the smoke temperature difference increases. Reason 1, through the coarse fine grinding coal, coal poor uniformity, improper adjustment of combustion, combustion of fuel is insufficient, serious mechanical incomplete combustion, and high levels of combustible ash accumulated in the back pass. 2, an oil burner or an oil poor atomization, so that unburned droplets deposited in the flue. 3, prolonged low load operation of boiler, the furnace temperature is too low or too small amount of excess air resulting in incomplete combustion of coal or oil accumulated in the tail. 4, after the shutdown of the fuel leakage into the furnace and accumulates or after shutdown and to insufficient MFT furnace purge unburnt coal or oil accumulation at the end of the tail. 5, soot blower failure, long-term put into operation is not normal. 1 process, when a slight secondary combustion, exhaust gas temperature does not rise within 20 ℃ normal smoking temperature should be checked immediately paragraphs, the combustion site and judge whether the secondary steam soot blowing. (When the exhaust gas temperature rises to 250 ℃) 2, the operation of the back pass and then generating boiler combustion boiler operation should be stopped immediately, immediately stop sending, ID fan and turn off all the smoke and steam soot blowing air damper fire. 3, if the economizer afterburning, until the storage tank level control valve blocking off without pressure, flow rate of feed pump motor start 150t / h Sheung be cooled. 4, air preheater heating surface of the secondary combustion air preheater normal operation, normal operation of the air pre-heater holder; air preheater Jam occurs, the main drive motor and the auxiliary drive motor trip, contact maintenance manual plate moving continuous air preheater rotor. Soot blowing steam into air preheater for extinguishing, into the air preheater for fire extinguishing can not be extinguished. 5, the economizer outlet water temperature close to the inlet temperature (at the economizer secondary combustion), the air preheater inlet gas temperature, exhaust gas temperature, the hot air temperature is lowered to less 80 ℃, each one hole, and the hole is no longer Mars smoke and soot blowing steam stops coming out after water or fire. Open hole inspection manhole and inspection to confirm the secondary combustion goes out, after the flue vent door open to drain water inside the smoke flue opening for ventilation air damper. 6, to be re-combustion is resolved, the flue temperature does not rise and fall when stabilized, before slow regulation of the air, smoke baffle, the necessary air cooling and purging.
Gas boiler safe operating procedures: gas-fired boilers this kitchen I believe we are not unfamiliar fishes it. But this thing is not so easy, and sometimes improper operation causing very serious consequences, so the gas boiler rules is very important. That in the end this is how the specific operation of it, if you want to know, quickly told us with a look. 1. All personnel must be familiar with the operation of the boiler performance and safety knowledge of the boiler operating certificates. This post is strictly prohibited non-operating personnel. Duty should be strictly in accordance with the operating records and do a good job shift recording, the security situation and the device should shift change operation tests, carried out. When the shift to check the boiler is intact. 2. Boilers and safety accessories should be inspected, and in the period. 3. Kai blast furnace gas furnace ready ① Check if the gas pressure is normal, not too high or too low, open the door of oil and gas supply section; ② Check whether the pump Sheung Shui, or opening the purge valve, until the Sheung Shui so far. Open the Water Supply System for each section of the door (front door section Sheung including pumps and boilers); ③ check level gauge, the water level should be in the normal position, the water level gauge, a water level required color plug in the open position, the water level to prevent false, if water can be manually Sheung; ④ check valves on the pressure pipe, must be opened, the wind deflector must all flue opening; each knob ⑤ checks the control cabinet are in their normal position; ⑥ 6t fired steam boiler for industry check valve should be in the closed state hot water boiler circulating pump outlet valve should be turned off; ⑦ checking water softening equipment is operating properly, a variety of indicators to create a soft water meets national standards. Open the power ⑴; ⑵ startup burner; ⑶ purge valve on the drum, is completely out of steam, the off; ⑷ inspection hole into the boiler, and the hand hole flange valves, the leak was found to be fastened, tight as the solid leakage maintenance shutdown; ⑸ pressure rise when 0.05 ~ 0.1MPA, replenishment, sewage, water supply systems and sewage screening test device while flushing water table; ⑹ when the pressure was raised to 0.1 ~ 0.15MPA, flushing pressure gauge trap; ⑺ when the pressure was raised to 0.3MPA, "fire load / small fire" knob to "fire" to strengthen the combustion; ⑻ when the pressure was raised to 2/3 of the operating pressure, start warming air supply tube, slowly open the main steam valve, to avoid water hammer; ⑼ drain valve is completely closed out of steam; ⑽ after all the drain valve closed, slowly open the main valve to open, and then half a turn; ⑾ "burner control" knob to " Auto "; ⑿ level adjustment: adjusting the water level (to manually start and stop the pump) according to a load, low load level should be slightly higher than the normal level, high load level should be slightly lower than the normal level; ⒀ steam pressure adjustment: adjusted according to a load combustion (manual adjustment Fire / small fire) ⒁ combustion state determination, determines the amount of fuel atomization air ⒂ observation condition exhaust gas temperature, smoke, temperature control is generally between 220--250 ℃ The flame color, smoke color, while observing the chimney exhaust gas temperature , concentration, adjusted to the optimum combustion state. ⑴ Open the power; ⑵ start the circulation pump; ⑶ slow circulation pump outlet valve; ⑷ startup burner; ⑸15 min "" Load fire / small fire "bit color button is turned to" fire "" ⑹ "burner control" knob spin to "automatic." 5A normal shutdown: hot water boiler ① "fire load / small fire" knob to "small fire"; ② off the burner; ③ close the fuel supply valve; ④ ⑤ closing dampers boiler after the temperature dropped to 50 ℃ , the circulation pump outlet valve closed. ⑥ stop circulation pump
Winter heating season is approaching, Jinan City, Shandong Province in response to the country clean, low-emission environmental requirements, increase efforts to support the promotion of winter heating clean, clean heating to further enhance the city level, issued on the issue clean winter heating engineering and operational capital subsidy Notice.
Second, the use of centralized gas boiler user, uniform implementation of preferential gas prices 1.71 yuan / cubic meter, the heating period and after the end of the third-party audit of gas consumption, gas will be the final settlement price (not exceeding Municipality department approved between the reference price) and 1.71 yuan / cubic meter price difference subsidy to the gas company, to purchase heating companies use non-city franchise gas pipeline business gas heating can be direct subsidies to heating companies.
Third, the use of electricity users centralized heating, heating period and by the end of the third-party audit by the electricity, the power company will operate the unit with the settlement price and preferential rates (level of 0.5 yuan / kwh, Valley Electric 0.25 yuan / kilowatt the difference between the time) subsidy to operate the unit.
Fourth, the use of formula household heating boiler user, purchase subsidy subsidy to the user equipment or units in accordance with Standard 2000 underwritten yuan / household. Temporarily performed using the sub-family user heating boiler gas prices during the step, performed in accordance with a first gear price urban gas prices; after the heating period, gas operation subsidies subsidies to users according to standard 1200 / household .
Fifth, the use of household electric heating type user, can also get subsidies. Subsidy ranges: The air source heat pumps, domestic electric boilers, heating cables, heating the carbon crystal plate user. According to the notification, the device according to the purchase subsidy subsidized purchase truly carbon crystal plate does not exceed 2,000 yuan / household air-source heat pump, domestic electric boilers, heating cables subsidy standard is 2000 Yuan / or household user to Advancer units. After the heating period, power to the user according to operating subsidies subsidies 1200 / standard household.Free Chat
Copyright © 2020.Company name All rights reserved.