After completion of the gas 6 ton industrial boiler cleaning, be sure to use hot air to dry them, but not both for heating the furnace walls and other accessories, this is likely to have adverse consequences. Right way is to place an electric heater in the bottom of the gas boiler, heated.
To further promote the comprehensive management of coal-fired 6 ton industrial boilers, Jincheng City, Shanxi Province, according to "Jincheng Blue win the Battle of three-year action plan" requirements, plans to complete 109 units of 10-20 tons of steam "small coal-fired boilers" within this year the phase-out, at the same time, Jincheng will start working out of 35 tons of steam coal-fired boilers.
This year, Jincheng counties (cities, districts) the environmental sector will urge the relevant enterprises and institutions to eliminate the basis of 10 tons of steam and coal-fired boilers on in 2018 to accelerate the phase-out and 20 tons of steam coal-fired boilers. This year, the city to complete 109 units (10-20 tons of steam boilers) working out of a total of 589.5 tons of steam boilers; at the same time, Jincheng will also speed up the foundation and 20 tons of steam coal-fired boiler out, start 35 tons of steam phase out coal-fired boilers, in principle, within the city's new domain-wide 35 tons of steam coal-fired boilers.
In addition, Jincheng will accelerate the transformation of ultra-low emission. Before the end of September this year, the city will complete 52 units (65 tons of steam per hour and higher coal-fired boilers) coal-fired heating boilers ultra-low total of 4530 tons of steam boilers transformation, and the county (city) built-up area, biomass boilers emissions transformation. After transformation, under condition of the reference oxygen content of 6%, soot, sulfur dioxide, nitrogen oxides emission concentration of these boilers respectively not higher than 10 mg / m, 35 mg / m and 50 mg / m.
Transformation of low nitrogen in the combustion aspect, before the end of October, Jincheng station 610 will complete the transformation of low-nitrogen combustion Total 1940.15 tons of steam gas boiler, after completion of the transformation, the boiler NOx emission will not exceed 50 mg / m.
What is the difference fired 6 ton industrial boilers and gas boilers in, why should phase out coal-fired boilers? From the nominal point of view, fuel gas boilers and coal-fired boilers obvious difference is the use of different, the former use of natural gas, which uses coal.
You must know the 6 ton industrial boiler energy problems (induced draft fan power consumption rate, steam consumption) draft fan causes problems 1.1 boiler flue dust and fouling, in particular air preheater fouling, resulting in increased resistance to smoke duct . 1.2 boiler flue, tail heating surface and dust leakage. 1.3 Leakage Rate large air preheater. 1.4 furnace excess air coefficient is too large. 1.5 unit load changes, run the adjustment is not timely, resulting in furnace pressure is too large. 1.6 unit load or low frequent starts and stops. 1.7 coal into the furnace worse, from the design value. 1.8 low efficiency filter. 1.9 draft fan blade badly worn, low operating efficiency. 1.10 fan outlet flue gas desulfurization big resistance. 1.11 soda boiler pipes for leaks. 2, 2.1 to 2.1.1 operational measures to solve the problem of the strict implementation of soot blowing system to prevent the heated area ash, blocking ash, flue gas system to reduce resistance. 2.1.2 holding the induced draft fan, the flue gas separator baffles and dampers in the fully open position. 2.1.3 The experiment showed combustion boiler, proper control of excess air in the furnace. 2.1.4 adjustment chamber negative pressure, air leakage reduction furnace and the flue. 2.2 routine maintenance and testing 2.2.1 induced draft fan performance test to determine the optimum operating point and efficient workspace. 2.2.2 boiler, air preheater, a flue, ESP and other system leakage inspection, process. 2.2.3 timely check processing chassis, shaft seal leakage. 2.3C / D repair, eliminating defects 2.3.1 down strict accordance with movement clearance adjusting fan. 2.3.2 induced draft fan blade defect action elimination hand vane opening adjustment. 2.3.3 Importers and induced draft fan baffle opening check. 2.3.4 duct tightness check process. 2.3.5 wave plate replacement air preheater, rinsed sector plate gap adjustment. 2.3.6 eliminate dust defects and improve collection efficiency. 2.3.7 clean flue gas desulfurization system, flue resistance is reduced. 2.3.8 eliminate soda boiler pipe leakage defects. 2.4A / B repair and transformation 2.4.1 Check and repair the fan blades, replace seriously damaged blades if necessary. 2.4.2 for energy saving fan efficiency below 75%. 2.4.3 The fan motor frequency transformation. 2.4.4 of the precipitator, if necessary, transform and improve collection efficiency.Free Chat
Copyright © 2020.Company name All rights reserved.