Cooperation with the fast boiler really is a very correct decision of our hospital. The party quickly boiler shell not only provides us with high-quality and high-performance energy saving boiler coexist; also provides free installation and post operation and maintenance personnel training services for our system, very caring, thoughtful. --customer feedback
Leakage Protection boiler manufacturers tell you tell you the importance of the importance of the boiler manufacturers leakage protection ----- i.e. drain leakage protection automatically cut off power; i.e., when the boiler water temperature overheat protection ultrahigh temperature reaches the alarm automatically stops the burner and alarm ; i.e., protection of the secondary superheater boiler housing temperature exceeds 105 deg.] C, operating system manufacturers to automatically cut off the boiler-like secondary circuit, the boiler is stopped; i.e. excellent anti-dry protection level electrode rod real-time monitoring water level, the boiler water level reaches the other reasons , below the low water level, the boiler stops working, to prevent the occurrence of dangerous dry. Glass wool insulation for whole body type, light weight, good thermal insulation effect, and less heat loss. White color board packaging, nice, closed Haonai corrosion, mechatronics, small footprint, and easy to use. Gas-fired boiler widely used in supermarkets, hospitals, schools, hotels, residential, bath center, fully automated for the user to provide bathing water or heating, domestic hot water. CWNS gas fired tube hot water boiler 1, the boiler hot water boiler manufacturers computer controller, all the functions are stored on a magic smart chip, a gas boiler steam boiler power key, automatic timing, temperature operation, the user can set startup, shutdown time, the setup is complete, no special duty to save time, and effort. 2 gas boiler, burner configuration imported brands, high degree of automation, automatic purge controller according to the instruction, the electronic auto-ignition, spontaneous combustion, air oil (gas) automatic ratio adjustment, security and stability performance, good combustion. And there are flameout protection device, ensure safe operation. 3, the inner fire tube inserted spoiler retardant, smoke slow speed, to strengthen the heat exchanger, the temperature of the flue gas discharged from a low smoke chamber, reducing heat loss and save fuel. 4, large font display temperature, easy to grasp and boiler operating conditions of the system, the water temperature can be freely set from 10 ℃ to 90 ℃, automatic boiler or heating system to provide users with life, bath with hot water.
How to maintain the boiler during operation of the boiler during operation how to maintain water supply and water quality monitoring furnace boiler feed water and boiler water boiler maintenance ⑴ should be consistent with GB / T1576-2008 "industrial boiler water quality" standards. And regularly sampled for testing. The number and frequency of emissions is determined by laboratory personnel. Laboratory and sewage should be detailed records. ⑵ mechanical rotation monitoring for pumps, fans, pumps, etc. to be employed a method of three touch see two monitors. Abnormal phenomenon, that approach to take. If necessary, to shutdown maintenance, are not the effect. ⑶ daily oil tank oil level monitoring if no automatic control device, the oil level should be checked regularly and found that the oil level is too low, the use of two hours is not enough, please notify the staff in advance of the fuel injected new fuel. ⑷ soft water tanks commonly used to control the operating state of the automatic control device ⑸ To periodically check the water treatment apparatus to the ion exchanger is failed, or periodically backwashed. ⑹ monitor the exhaust gas temperature under normal circumstances, the new boiler is generally lower exhaust gas temperature, with the increase in run time will gradually increase. If it is found that the change is too large and exceeds 20 ℃ (algebraic difference), you should select the appropriate cleaning shutdown time. If this phenomenon occurs very frequently, it will have to check whether the normal combustion system. The oil pressure is too low, resulting in poor atomization low oil temperature, oil or wind than not, resulting in poor fuel air mixture so that the char combustion analysis hypoxia. Further, the dry back boiler, if the exhaust gas temperature increased abruptly, it is possible to return in a compartment between the second and third after the smoke box backhaul firewall leak smoke, shutdown would need repair.
Oven before the gas fired tube hot water boiler should have conditions: ① boiler ended conduit means passing the fire test pressure. ② furnaces wall, holding full of things end, acceptance pass. ③ smoke duct means end, the end of incubation, the induced draft fan receiving apparatus failed commissioning. ④ oven cold working means necessary electrical instrumentation, calibration pass. ⑤ An delineated request being through the external cold mortar mix is bilateral shelved. ⑥ oven with wood, diesel oil, coal and all kinds of things (including review, site lighting, etc.) Preparatory end. ⑦ Ovens way to fully rely on the device, and has nothing to do and the way to take Ovens full withdrawal, liquidation garden shabby. ⑧ Ovens staff trained qualifiedFree Chat
Copyright © 2020.Company name All rights reserved.