Wuhan Port District Social Welfare Institute (apartments for the elderly) is invested by the government pension services, with a total construction area of 38,000 square meters, 532 beds, mainly adopt destitute persons, social support on behalf of the elderly. Hope to provide welfare to the elderly year-round 24-hour hot water, the original boiler equipment can not meet this demand, therefore, require additional purchase orphanage hot water boiler. After much investigation, in cooperation with the welfare determined fast boiler, provides three integrally condensing gas hot water boiler (WNS1.4-1.0 / 95/70-Y.Q) by a fast boiler.
Primary air tube blockage is what causes? How to prevent? Reason: 1) blocked or coked-burner fire nozzle inlet is blocked portion of small oil gun and other debris. 2) too many impurities coal, powder machine speed is too high, the pulverized coal and primary air speed too low. 3) powder machine speed is too high, too much under the powder without timely blown away. 4) a low pressure (throttle open or not to open too small), can not take away meal. Precautions: 1) to the powder and the rotational speed of the unit load and adjust relevant primary pressure according to the powder not more than 700 rpm rotation speed, a wind speed of each holding 25 ~ 30m / s, the mixed primary air temperature was controlled at 180 to 250 ℃, a pressure depending on the load, depending on coal, in the range 2.5 ~ 3.8kPa. 2) find a wind speed is too low, the primary air temperature is lower than the normal value should be to lower the rotation speed corresponding to the normal to the powder of a primary air temperature and wind speed. 3) open, gas 2t diesel fired steam boiler tank should be fully cut-off torch powder, the powder in the tube is blown accumulated powder. 4) Fire mouth clogged or coked should try to remove. What causes large vibrations induced draft fan? 1) motor bearings in oil, resulting in large vibration and bearing wear; 2) even when the shaft is mounted on the center not good; 3) induced draft fan stall surge; 4) anchor bolt loosening induced draft fan; 5) blade fouling or wear ,lost balance.
Gas oil furnace fuel additive effect and the boiler room Notes: Gas oil furnace, oil furnace that is both in one, and, still in the boiler in this category, so, based on this, the following will continue be familiar with and understand the boiler, because it is the product website and keywords. Moreover, we can also derive some new knowledge, in turn, make progress and development in their learning path. 1. Gas oil furnace, which is a fuel additive, then what good? Gas conducting oil furnace, in which fuel additives, it is possible to optimize the fuel, and reducing soot and improving thermal efficiency. However, it should be noted that, in addition amount to control the well, in moderation, too much or too little, will always have problems, thereby, affecting the normal combustion of the fuel. 2. Gas-fired 2t diesel fired steam boiler and gas oil furnace, boiler room can both jointly built it? Gas-fired steam boiler and gas oil furnace, two boiler room, is jointly built, and that is no problem. However, it should be carried out in accordance with the steam boiler room equipment specifications and oil furnace room design specifications, avoid mistakes, and at the same time, to make the two boilers, a good use of effects.
What are the technical parameters of the gas boiler boiler parameters are: 1, boiler capacity, which is the output Q, units of 2t diesel fired steam boilers are tons / hour representation. Hot water boiler for heat MW / h represents; 2, pressure P, the unit is Mpa; 3, steam (or superheated steam) Temperature q, in degrees Centigrade. Hot water boiler expressed in terms of outlet temperature and return water temperature. Another area of the heating surface of each grate area, fuel type, fuel consumption, water temperature, total drag, with the wind (the wind drums) the amount of exhaust gas temperature and the like. The expression model are: the number of drum (e.g., single drum D, S, double drum); drum arrangement (transverse type H, the Z vertical type); combustion (chain L, G stationary grate etc.); a fuel type (coal a, gas Q, Y fuel, etc.); a steam boiler is usually "tons / h" or "t / h" is the capacity of the boiler. With "Mpa" or "MPa" (old unit of "kgf / cm 2" or "kgf / cm2") of the rated pressure of the boiler, it represents the temperature at the rated pressure saturated steam and superheated by "deg.] C" (Celsius) steam temperature. Thermal Efficiency Heat Transfer Fluid is a boiler furnace or a thermal transfer process, heat is absorbed by water, steam or thermal oil, accounting for complete combustion of the fuel into the boiler heat released percentage capacity of 1t / h steam boiler, i.e. It indicates that the boiler may be over 1 hour into water of 1 ton capacity of saturated steam under pressure; 0.7MW of such water heaters and furnaces heat Transfer Fluid representations may generate heat corresponding to 0.7MW power over 1 hour ( equivalent to one ton of steam heat). Two water boiler is the heating means for the hot water boiler working fluid. Usually "MW" (MW), with the old unit "when Wan kW /" or "million kcal / h", namely "104kcal / h" is the capacity of the boiler, with "Mpa" represents the rated pressure of the boiler, with "℃" the hot water temperature.Free Chat
Copyright © 2020.Company name All rights reserved.