Primary air tube blockage is what causes? How to prevent? Reason: 1) blocked or coked-burner fire nozzle inlet is blocked portion of small oil gun and other debris. 2) too many impurities coal, powder machine speed is too high, the pulverized coal and primary air speed too low. 3) powder machine speed is too high, too much under the powder without timely blown away. 4) a low pressure (throttle open or not to open too small), can not take away meal. Precautions: 1) to the powder and the rotational speed of the unit load and adjust relevant primary pressure according to the powder not more than 700 rpm rotation speed, a wind speed of each holding 25 ~ 30m / s, the mixed primary air temperature was controlled at 180 to 250 ℃, a pressure depending on the load, depending on coal, in the range 2.5 ~ 3.8kPa. 2) find a wind speed is too low, the primary air temperature is lower than the normal value should be to lower the rotation speed corresponding to the normal to the powder of a primary air temperature and wind speed. 3) open, gas best steam boiler prices tank should be fully cut-off torch powder, the powder in the tube is blown accumulated powder. 4) Fire mouth clogged or coked should try to remove. What causes large vibrations induced draft fan? 1) motor bearings in oil, resulting in large vibration and bearing wear; 2) even when the shaft is mounted on the center not good; 3) induced draft fan stall surge; 4) anchor bolt loosening induced draft fan; 5) blade fouling or wear ,lost balance.
Fang fast, based on the boiler industry, the rise in clean-burning, low-nitrogen management in a more environmentally friendly. In the family group when Mr. Lu Haiqing's correct leadership, we deepen the industrial revolution, brought together the group cohesion, pioneered premix, FGR low nitrogen and other advanced processing technology and products in the industry; more than 100 national patents so that we in the industry chasing; unique cloud service remote control system for boiler intelligent control. Anyang City, the first batch of standards implementation of intellectual property rights demonstration units, the industry's first high-tech digital exhibition hall, China's first put into practical operation of the low nitrogen boiler ...... party fast data demonstrate, to speak with strength.
Gas-fired best steam boiler prices will need to follow those steps: Due to the special nature of dual-use oil and gas boilers, thereby preparing the initial installation and construction from its long-term project to the acceptance stage there will be any problem to pay attention to the need to comply with, what does? Gas-fired steam boiler needs to follow the procedure step by step to complete. In this process, the need to comply with, what does? Boiler installation and construction of oil and gas dual front, first in accordance with the procedures to handle boiler installation approval procedures, pending approval of Quality and Technical Supervision after!
Steam boiler preventive measures introduced Common Failures and precautions best steam boiler prices and steam reciprocating pump 1. Biomass boiler is a kind of boiler to biomass energy as a boiler fuel called biomass boilers, steam boilers into biomass, biomass hot water boiler, biomass stove, biomass thermal oil heaters, vertical raw biomass boilers, biomass boilers and other horizontal. Fuel gas boiler is not only fuel but also refers to the gas boiler. Previously no such dual-fuel boiler, burner because either fuel or gas, no dual fuel burners. With the rapid development of the world energy equipment, some European countries begin production and sales of fuel gas burner, dual fuel burner and boiler combination of organic birth of a new breed of boiler - fuel gas-fired boiler. Near the steam boiler room should be equipped with adequate and effective fire fighting equipment. 2. Steam boiler room must have staff on duty 24 hours, the guards take turns, and always check the water level in the boiler, in order to ensure that it is above the safety line to prevent an explosion caused by burning dry. If the fire operation in explosive areas must obtain a work permit fire and take adequate fire safety measures in order to carry out fire work. When the fire should send someone on duty at all times observe the fire situation. 3. A storage vessel containing the non-flammable gas in the boiler room. 4. The staff of steam boiler room must be certified before the arrival of the boiler and proficient technique, it has a certain capacity to detect and recognize security risks. 5. If the boiler safety on a regular basis in accordance with the boiler maintenance procedures, should be carefully examine each of insecurity in the inspection process. 6. Distribution Line steam boiler room disposed defective safety device using a metal tube or pipe nonflammable hard plastic protection switch box should be installed outside the boiler room, respectively, to achieve power, should be prohibited. 1. What is the reason there is no discharge of steam reciprocating pump is? How, how? A: (1) Failure: 1 suction or discharge pipe blockage. (2) out of the stuck valve. There is an air cylinder. (4) a suction tube connected lax. (5) column (live) seriously damaged piston ring. (2) Method excluded: (1) exclusion of pipe blockage. (2) Remove the inlet, the outlet valve on the plug. (3) filled with water, the air is discharged. (4) fastening the pipe. (5) Replace Column (live) piston ring.Free Chat
Copyright © 2020.Company name All rights reserved.