1: Steam boiler steam pressure the higher the better selection pressure, depending on the user's requirements. Vapor pressure, safety pressure member Advantageously, the energy consumption is low; but the steam will be relatively worse quality, low enthalpy, humidity, may be difficult to meet the disinfection, sterilization, culture, heating and power needs. And the high vapor pressure, energy consumption is high, the corresponding steam equipment, piping and valves the pressure is high, the maintenance requirements are also more, the production of steam, the heat transfer process, a large leakage loss. Meanwhile, high-pressure steam as the steam pressure is increased to carry the increased salinity, so salinity these waterwall tubes, pipe tobacco, and other drum heating surface fouling, overheating, foaming, clogging even increase the possibility of squib. Salt steam to steam turbine flow area will decrease, reducing the efficiency and seriously affect the heat transfer. Thus, fireman must operate in accordance with operation of the steam pressure, the steam pressure fluctuations generally allows a value between 0.05 ~ 0.15MPa.
2: the higher the boiler water level was considered safe water level is higher, the boiler water is not easy, security is also guaranteed. In fact, this is a misconception, the water level is too high, steam and humidity increase, poor steam quality, steam equipment will harm and production results. Industrial boilers, a moisture vapor sterilization or incubation with a large amount of steam also increased salt, or culture for a long time ranging from sterilization, steam consumption increase, ineffective, decreased production culture; weight is not reached the purpose of disinfection or cultured biological products contaminated scrap, even pipes, water hammer occurs apparatus. For utility boilers, steam moisture capacity, the steam turbine last stage blades will be erosion, there may appear Priming pot, water shock severe enough to cause harm equipment and personal safety. Thus, the pot water level should be maintained within a fluctuation range of ± 50mm well.
3: Some people think the better fuel plus fuel plus the more productive the greater the amount of steam. Little do they know too much fuel into the furnace, the effect will be counterproductive. When a certain amount of air and the excess amount of fuel, the furnace will produce a large amount of incomplete combustion, resulting in energy waste. People often see the dark furnace flame, weakness, and black smoke chimney, mostly for this reason. In severe cases, there will be fire pulverized coal, oil furnace secondary combustion occurs, burst pipes until shutdown. Therefore, the ratio of fuel and air volume should be adjusted appropriately, typically by looking at the fire, smoke color look, see table indicates the amount of oxygen determined. When the flame in the furnace as a bright yellow, pale gray smoke chimney to take, stable vapor pressure, wind coal showed appropriate ratio, good combustion.
4: Dial stirring the fire, the better the fire is commonly used in industrial boilers manual method. By stirring the fire, can be eliminated crater, reduction furnace from the fire and the fire bed smooth, homogeneous combustion, strong. But too much stirring the fire, but will reduce the overall thermal efficiency; this is because when stirring the fire, a lot of cold air into the furnace, reducing the average temperature of the furnace section of the flame. At the same time, increase the heat losses, an increase in the number of black smoke chimney, pollution of the environment. In addition, when stirring the fire, the staff is also susceptible to flame radiation, burns, fire-resistant layer is also susceptible to dial hearth fire damaged tools, increased furnace building maintenance workload. Therefore, the fire should be allocated as needed, to minimize the appropriate dial.
5: the bigger the better furnace pressure and furnace pressure is reflected in one of the boiler combustion conditions is normal or not an important parameter. Operating the boiler furnace negative pressure should be maintained between 10 ~ 20Pa, too great a negative pressure results in: increased leakage furnace, heat losses increase; wind increased electrical energy consumption; fly ash increased the wear along the heating surface; reduced the furnace heat of combustion efficiency. Most gas-fired boiler designed to run slightly positive pressure to increase the combustion rate. Operation, the furnace pressure becomes positive, even increasing the wind is still difficult to maintain the chamber negative pressure, said system failure or the wind furnace wall tubes, superheaters and other soft drinks leakage; fire furnace, the furnace pressure is first reflected table violent swing to the negative direction flung head. Therefore, the furnace pressure must be run according to the provisions, or should pinpoint the cause.
6: sewage longer the better spoken here regularly refers only to the sewage discharge rather than continuous blowdown. Periodic sewage mainly refers to the existence of negative bottom of the boiler slag, dirt and corrosion products, reduce furnace tube fouling, prevent clogging and reduce the salt content of the water boiler, heat transfer enhancement effect. One would think that the longer the discharge time, impurities will be discharged bottom of the pot the more, the better sewage, it is not. Sewage long time, a waste of a lot of heat, affect heating steam pressure; two pairs of boiler water circulation unfavorable, water wall tube burst will occur in severe cases. Thus, the sewage must be periodically according to "ground discharge, the discharge less uniform row" principle, provided hand operation. General Provisions at least once every eight hours of sewage, sewage each time shall not exceed 30s, overtime is strictly prohibited.
Zhengzhou Sunrise Optoelectronics Technology Co., Ltd. by the Dongxu Group, Henan Province, the state-owned asset management companies and Zhengzhou Investment Holdings Limited jointly made, mainly engaged in flat panel display and solar industry design materials, manufacturing and sales operations. Sunrise Optoelectronics project has been put into a production line, the second phase will continue the expansion, three new production lines to meet the production needs of Project Phase II, Sunrise Optoelectronics urgent need to increase new boiler equipment. After investigation and screening of a number of boiler brands, determined to cooperate with the fast boiler, steam signed a 10-ton integrated condensing gas steam boiler (WNS10-1.25-Y.Q).
Application of electric steam boiler steam boiler in the electrical industry applications in various industries ironing washing industry: dry-cleaning machine, dryer, washing machine, dryer, ironing machine, iron, and other equipment for use. Food Machinery Industry: supporting tofu machine, steamer, pot sterilization, packaging machines, coating equipment, sealing machine, and other equipment to use. Supporting the use of fermentation tank, reactor, sandwich pot, mixer, emulsifier and other equipment: bio-chemical industry. Other industries :( oil, automobile) steam cleaning industry (hotels, dormitories, schools, mixing station) hot water supply, (bridges, railways) concrete curing, (casual beauty club) sauna, hot swap equipment.
Steam Gas Gas Desulfurization to achieve excellent results steam oven gas steam oven must sample tests, the thermal conductivity was measured quality of appearance, flash point, viscosity, acid, water, and carbon residue, provided with heat transfer fluids plant proof mass It is consistent with the book, but also provide the basis for future changes in the operation of medium quality monitoring. Means passing the tests of the gas-steam heat transfer fluids using pumps to transfer fluids within the furnace and the injection of hot expander. When pumps heat transfer fluid to the injection system, should check again the furnace, heating equipment, piping system drain valve, drain valve is closed, in order to avoid loss of heat transfer fluids. While the exhaust pipe and the valve opening on the furnace one by one, to exclude air, until a closed gas steam flows. It stops when the oil level gauge appears on the expander injection heat transfer fluids, and then start the circulation pump, for circulating cold. Existing gas steam oven dry dust, do not meet wet desulphurization process of flue gas CWS humidity, water vapor in the flue gas as coal-water slurry up to 36%, some as high as 40% or more water content of coal-water slurry, If we consider only the dust and sulfur dioxide that is not enough. Arts gas steam boiler company after multi-party experts to study, test, develop a dusting product, the successful use of coal-water slurry plenty of water in the flue gas as a carrier, by cooling, reducing condensation, dust and sulfur dioxide capture down, to achieve excellent results gas desulfurization steam oven. The effect of dust reaching the user's satisfaction. Gas welding gas steam oven must be operated by welders holding boiler and pressure vessel certification of welders. Welding dimensions meet the design drawings and process documents, bead height is not less than the base material, the base material with a smooth transition. Gas fuel gas steam oven weld and heat affected zone no cracks, holes, craters and slag. Weld undercut hole deeper than 0.5mm, the total length (the sum of both) is not more than 1/4 of the circumference of the tube, and not more than 40mm. Construction of gas steam oven strict compliance with welding procedures and other relevant standards and regulations, and make construction records welded to record the record.Free Chat
Copyright © 2020.Company name All rights reserved.