You must know the combined 8 ton boiler dealer energy problems (induced draft fan power consumption rate, steam consumption) draft fan causes problems 1.1 boiler flue dust and fouling, in particular air preheater fouling, resulting in increased resistance to smoke duct . 1.2 boiler flue, tail heating surface and dust leakage. 1.3 Leakage Rate large air preheater. 1.4 furnace excess air coefficient is too large. 1.5 unit load changes, run the adjustment is not timely, resulting in furnace pressure is too large. 1.6 unit load or low frequent starts and stops. 1.7 coal into the furnace worse, from the design value. 1.8 low efficiency filter. 1.9 draft fan blade badly worn, low operating efficiency. 1.10 fan outlet flue gas desulfurization big resistance. 1.11 soda boiler pipes for leaks. 2, 2.1 to 2.1.1 operational measures to solve the problem of the strict implementation of soot blowing system to prevent the heated area ash, blocking ash, flue gas system to reduce resistance. 2.1.2 holding the induced draft fan, the flue gas separator baffles and dampers in the fully open position. 2.1.3 The experiment showed combustion boiler, proper control of excess air in the furnace. 2.1.4 adjustment chamber negative pressure, air leakage reduction furnace and the flue. 2.2 routine maintenance and testing 2.2.1 induced draft fan performance test to determine the optimum operating point and efficient workspace. 2.2.2 boiler, air preheater, a flue, ESP and other system leakage inspection, process. 2.2.3 timely check processing chassis, shaft seal leakage. 2.3C / D repair, eliminating defects 2.3.1 down strict accordance with movement clearance adjusting fan. 2.3.2 induced draft fan blade defect action elimination hand vane opening adjustment. 2.3.3 Importers and induced draft fan baffle opening check. 2.3.4 duct tightness check process. 2.3.5 wave plate replacement air preheater, rinsed sector plate gap adjustment. 2.3.6 eliminate dust defects and improve collection efficiency. 2.3.7 clean flue gas desulfurization system, flue resistance is reduced. 2.3.8 eliminate soda boiler pipe leakage defects. 2.4A / B repair and transformation 2.4.1 Check and repair the fan blades, replace seriously damaged blades if necessary. 2.4.2 for energy saving fan efficiency below 75%. 2.4.3 The fan motor frequency transformation. 2.4.4 of the precipitator, if necessary, transform and improve collection efficiency.
Beijing New Energy Automobile Co., Ltd. is China's first to operate independently and gain new energy automobile production qualification of new energy auto companies, mainly engaged in new energy vehicles and key parts and components research and development, production, sales and service business segments, and the layout intelligent manufacturing, energy management, smart travel, Internet +, and other strategic emerging industries. In the new energy automobile manufacturing process, and a series of paint drying processes can not do without the help of hot water combined 8 ton boiler dealer. Due to the company before the device has reached less than the growing production needs, the introduction of the 2017 mid-tail electric company producing heating pressure hot water boiler (CEDR0.7--95 / 70-Ⅱ).
Third, the natural gas steam boiler
Gas-fired steam combined 8 ton boiler dealer abnormal situation, how should we deal with it? When we use gas steam boiler, failure or abnormal phenomena it is inevitable, but in order not to affect the normal use, in the event of a problem gas steam boiler to be timely processing solutions, then the face of all kinds of circumstances, we should how to handle it? Share some of the ways we deal with unusual circumstances. If only gas steam boiler circulating pump abnormalities, such as its current decreases, the pump outlet pressure back to zero, which indicates no oil pump is idle, it may be caused by oil vaporization. Yang identify the reasons therefore first vaporized measures; such as clogging of the filter circulating pump bypass opening evacuated immediately clean the filter; heat transfer fluid as a result of added aqueous or decomposed gases are not excluded in the system, should immediately open the vent an exhaust valve. Circulation pump pressure constant, the current increases and the flow drops, deterioration of the thermally conductive fluid, the viscosity increased, should be replaced or regenerated. New heat transfer fluid as a result of decomposition of aqueous or excluded gases in the system, should immediately open the vent valve of the exhaust gas. When the current is lower than normal circulation pump, the circulation pump efficiency is decreased, the flow rate decline may be heating pipes plug fouling, stainless steel chain should be cleaned. If the gas steam boiler before and after the filter increased in pressure, the pump inlet pressure drops, the filter may be stuck, the opening of the bypass, disassemble and clean the filter. In addition to its low furnace outlet temperature liquid phase heat carrier, mainly for lack of heat fouling problems, it is timely soot blowing. Gas steam boiler grate more common problem is stuck, there are reasons including breaking grate or the grate off loose pins; coal grate has stuck to metallic inclusions; arched grate; slag is sinking the tip of the grate stuck. In response to this phenomenon, the required reverse hand grate plate debris removal, replacement breaking grate after the start, then jammed as startup, stop the rotation of the reasons detailed inspection to resolve. But also to re-adjust the adjustment screw on both sides of the grate tension, if still does not work, we need to replace the sprocket.Free Chat
Copyright © 2020.Company name All rights reserved.