Gas introduced gas 15 ton steam boiler steam boiler stop sign Profile: natural gas steam boiler is a steam boiler gas, natural gas steam boiler with natural gas as fuel, the combustion in the furnace heat put out by heating the pot water, and allowed to vaporized into steam energy conversion device. Water pan (drum) is continuously released from the combustion of a gaseous fuel energy to heat the furnace temperature is increased and produce steam under pressure. Since the boiling point of water increases with increased pressure, the pot is sealed, the expansion of water vapor generated inside the pressure limited thermodynamic formed, strictly speaking, the steam boiler is heated in water at constant pressure saturated steam drum regasification water formed, is widely used as an energy source. Protection device: (1) protect the boiler water a boiler water level gauge plate supporting one to two, should always be compared with each other, inconsistent findings indicate that shall be corrected immediately. Class water level should be flushed, to determine their true level. While the water level comes electrode rod can accurately capture level signal to an alarm or a pump control. (2) steam pressure protection pressure controller: selection of high sensitivity of the pressure controller, the pressure is high, or low levels of signal to the electrical switches, other control lines or automatic control chain protection. Using pressure controllers and electrical contacts, the vapor pressure can overpressure alarm; single adjustable pressure controller or dual fire burning fire the actual operating pressure. Safety valve: safety valve is the last line of defense to protect the boiler, the boiler pressure exceeds the limit, according to the set pressure relief valve design with the school, the exhaust steam pressure relief, to ensure the normal operation of the boiler. (3) having a burner flame protection flame protection inlet means, combustion function is to detect, when the ignition failure or extinguish combustion middle, immediately off the burner into the oil (gas) solenoid valve, the blower continues to operate at this time, the furnace was purged combustible residual gas, after 20 to 30 seconds purge, and various auxiliary blowers automatically cut off power, the boiler operation stops. (4) self-locking power failure protection case, the boiler shutdown immediately burst self-locking power interruption, if the current power is restored, the boiler will not start at any time, you must reset release self-locking, to re-start the ignition. Editing boiler ignition procedures: 1. Check operation and (or) shift recording. 2, inspection, examination boiler, external. 3, check the main safety accessories. Safety valve, water gauge, pressure gauge, to be tight, reliable and sensitive. 4, check the water treatment equipment. 5, inspection equipment and soda water supply system pipe. Adjust the valves as required to start. 6. Check the oil supply equipment. After the above inspection qualified, you can start the boiler. Note: The boiler is a high-temperature, high-pressure thermal equipment, is one of special equipment, widely used in government agencies, public companies and all walks of life, it is dangerous and special equipment. Event of an accident involving public safety, it will cause huge losses to the state and people's lives and property. For public safety, people's lives and property safety, according to the State Council, "Regulations on Safety Supervision of Special Equipment", the boiler should use full attention the following matters: 1, should be accompanied by safety technical specifications of the factory boiler design documents, product quality certification, safety and the use and maintenance instructions, supervision and inspection certificate (safety supervision, inspection and performance certificate). 2, boiler installation, maintenance, alteration. Engaged in the installation of the boiler, maintenance, renovation of the unit shall obtain special equipment installation and maintenance certificates issued by the Provincial Quality and Technical Supervision, before engaging in the boiler installation, maintenance, alteration. Construction unit before construction will be prepared for installation, maintenance, alteration in writing inform the special equipment safety supervision and management department of the municipality or district, and will start informing sent to the local county level Quality and Technical Supervision for the record, told immediately after construction. 3, inspection of boiler installation, maintenance, transformation. After construction, the construction unit To State Quality and Technical Supervision of Special Equipment Inspection and hydrostatic testing of the boiler installation supervisory inspection declaration. After passing by the State Quality and Technical Supervision, State Special Equipment Inspection, County of Quality and Technical Supervision involved in overall acceptance. 4, registration boiler. After the boiler inspection, the use of units must be in accordance with the "special equipment registration and use of management rules", fill "boiler (census) Registration Form", the State Quality and Technical Supervision to register and obtain a "registration certificate to use special equipment safety . " 5, operation of the boiler. Boiler operation must be performed by trained and qualified to obtain "special equipment operator certificate" certified personnel to operate, must strictly abide by the rules and eight systems, six record. 6, check the boiler. Periodic inspection of boiler once a year, not be used without safety periodic inspection of boilers. Safety accessories safety valve of the boiler regular inspection once a year, pressure gauge biannually verified, may not be used without the periodic inspection of the safety accessories. 7, non-pressure boilers will be installed for the boiler pressure. Do not use water level gauge, safety valve, pressure gauge three safety accessories insufficiency boiler.
Fast Boiler Co., Ltd. is a really truly think about your clients practical solutions to business problems, this recommendation after this water-tube boilers put into use, the quality inspection departments, the nitrogen oxide emissions, soot and other indicators They are in line with national standards, but also very full of fuel combustion, high thermal efficiency, saves us a lot of fuel costs. This cooperation, I am very satisfied. --customer feedback
The scaling of gas-fired 15 ton steam boiler not only reduces the thermal efficiency of the boiler, but also increases the temperature of the heating surface of the boiler, causes damage to the heating surface, and even causes the explosion accident of the boiler. Therefore, the use of soft water treatment equipment, strictly according to the process operation of boiler feed water softening treatment equipment, control boiler feed water quality, can delay the formation of the scale. At the same time, it is very important to control the boiler scale in real time, master the boiler scale and clean the scale if necessary. Because the temperature of the gas-steam boiler body and the steam-water heat pipe system is higher than the air temperature in the boiler room, some of the heat is emitted through radiation and convection into the surrounding air. This becomes a loss of heat. Boiler Therefore, the heat loss should be reduced when the heat insulation and heat pipe system of the boiler are damaged or leakage is discovered. The increase in noise from gas-fired steam boiler burners is mainly due to the closure of the valve or insufficient oil intake in the oil path, blockage of the oil filter, or because of low inlet temperature, high viscosity or oil on the pump. Too high temperature; oil pump failure; fan motor bearing damage; due to dirty turbine impeller, the equipment is too loud. This failure occurs when a gas-fired boiler is in use and is not easy to atomize (heavy oil) because of the high viscosity of the oil; it is also due to cyclone and jet The distance between the nozzles is inappropriate; in addition, because the burner is worn or dirty; it is also due to the excessive heating temperature of the spare fuel tank, resulting in steam pumping the oil pump out of the oil pump; or because the oil in the oil boiler is hydrated. Gas steam boiler feed water contains a variety of impurities and calcium, magnesium and other scaling substances, the boiler will inevitably expand. The thermal conductivity of the scale is very low, so once the surface is polluted by the hot surface, the exhaust temperature of the boiler will increase, and the heat loss of the exhaust gas will increase due to the increase of the thermal resistance. The experimental data show that the heat loss of waste gas will be increased by about 2%-4% when 1mm oxide is formed on the heating surface of boiler. The thicker the scale on the heating surface of the boiler, the greater the thermal resistance, and the lower the thermal efficiency of the boiler.
There are many types of steam oil-fired boilers followed by the main uses, main features, a brief introduction to the automatic oil-fired gas-fired steam boilers.1: main uses: fully automatic fuel-fired gas-fired steam boilers provide production steam for food processing, printing and dyeing, pharmaceutical production, disinfection steam for medical institutions, and steam for heating of other enterprises and guesthouses. Domestic hot water can also be provided by water tank heating. Two: main characteristics: 1, adopt the central reburning structure, boiler water volume and gas space is large, adaptive load ability is strong. 2. The flame is burned under micro-positive pressure in the fully automatic steam oil-fired boiler, the flame extends completely, and the heat transfer is enhanced, thus the convection heating area is reduced and the boiler cost is reduced. The flow resistance of flue gas is small and the power consumption is low, so the operation cost can be saved. 3, in addition to the traditional four water level height control, add the fifth water level detection, the boiler will stop when the water shortage occurs, alarm, ensure the safety of boiler operation.Free Chat
Copyright © 2020.Company name All rights reserved.